
<pat:PatentPublication xmlns:pat="http://www.wipo.int/standards/XMLSchema/ST96/Patent" xmlns:xsi="http://www.w3.org/2001/XMLSchema-instance" xmlns:com="http://www.wipo.int/standards/XMLSchema/ST96/Common" com:st96Version="V7_0" com:documentFileName="OPENDATAST96_PT_CZ_DIFF_PUV2025-42970.xml" com:languageCode="cs" xsi:schemaLocation="http://www.wipo.int/standards/XMLSchema/ST96/Patent https://isdv.upv.gov.cz/doc/xsd/ST96/PatentPublication_V7_0.xsd">
 <com:IPOfficeCode>CS</com:IPOfficeCode>
 <pat:BibliographicData com:st96Version="V7_0" com:officeCode="CZ">
  <pat:PatentPublicationIdentification>
   <com:IPOfficeCode>CZ</com:IPOfficeCode>
   <pat:PublicationNumber>38860</pat:PublicationNumber>
   <com:PatentDocumentKindCode>U1</com:PatentDocumentKindCode>
   <com:PublicationDate>2025-10-07</com:PublicationDate>
  </pat:PatentPublicationIdentification>
  <pat:ApplicationIdentification>
   <com:IPOfficeCode>CZ</com:IPOfficeCode>
   <com:ApplicationNumber>
    <com:ApplicationNumberText>2025-42970</com:ApplicationNumberText>
   </com:ApplicationNumber>
   <com:FilingLanguageCode>cs</com:FilingLanguageCode>
   <pat:ApplicationFilingCategory>National</pat:ApplicationFilingCategory>
   <pat:FilingDate>2025-06-30</pat:FilingDate>
  </pat:ApplicationIdentification>
  <pat:PriorityClaimBag>
   <pat:PriorityClaim com:sequenceNumber="1">
    <com:IPOfficeCode>CZ</com:IPOfficeCode>
    <pat:FilingDate>2025-06-30</pat:FilingDate>
    <pat:ApplicationFilingCategory>National</pat:ApplicationFilingCategory>
   </pat:PriorityClaim>
  </pat:PriorityClaimBag>
  <pat:PatentClassificationBag>
   <pat:CPCClassificationBag>
    <pat:MainCPC>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20141201</pat:ClassificationVersionDate>
      <pat:CPCSection>H</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>S</pat:Subclass>
      <pat:MainGroup>40</pat:MainGroup>
      <pat:Subgroup>32</pat:Subgroup>
      <com:SymbolPositionCode>F</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>I</pat:CPCClassificationValueCode>
      <pat:ActionDate>20250908</pat:ActionDate>
      <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
    </pat:MainCPC>
    <pat:FurtherCPC>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20141201</pat:ClassificationVersionDate>
      <pat:CPCSection>H</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>S</pat:Subclass>
      <pat:MainGroup>40</pat:MainGroup>
      <pat:Subgroup>38</pat:Subgroup>
      <com:SymbolPositionCode>L</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>I</pat:CPCClassificationValueCode>
      <pat:ActionDate>20250908</pat:ActionDate>
      <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
    </pat:FurtherCPC>
   </pat:CPCClassificationBag>
   <pat:IPCRClassificationBag>
    <pat:IPCRClassification com:sequenceNumber="1">
     <pat:ClassificationVersionDate>20140101</pat:ClassificationVersionDate>
     <pat:PatentClassificationLevelCode>A</pat:PatentClassificationLevelCode>
     <com:SymbolPositionCode>F</com:SymbolPositionCode>
     <pat:IPCClassificationValueCode>I</pat:IPCClassificationValueCode>
     <pat:ActionDate>20250908</pat:ActionDate>
     <pat:IPCClassificationStatusCode>B</pat:IPCClassificationStatusCode>
     <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
     <pat:Section>H</pat:Section>
     <pat:Class>02</pat:Class>
     <pat:Subclass>S</pat:Subclass>
     <pat:MainGroup>40</pat:MainGroup>
     <pat:Subgroup>32</pat:Subgroup>
    </pat:IPCRClassification>
    <pat:IPCRClassification com:sequenceNumber="2">
     <pat:ClassificationVersionDate>20140101</pat:ClassificationVersionDate>
     <pat:PatentClassificationLevelCode>A</pat:PatentClassificationLevelCode>
     <com:SymbolPositionCode>L</com:SymbolPositionCode>
     <pat:IPCClassificationValueCode>I</pat:IPCClassificationValueCode>
     <pat:ActionDate>20250908</pat:ActionDate>
     <pat:IPCClassificationStatusCode>B</pat:IPCClassificationStatusCode>
     <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
     <pat:Section>H</pat:Section>
     <pat:Class>02</pat:Class>
     <pat:Subclass>S</pat:Subclass>
     <pat:MainGroup>40</pat:MainGroup>
     <pat:Subgroup>38</pat:Subgroup>
    </pat:IPCRClassification>
   </pat:IPCRClassificationBag>
  </pat:PatentClassificationBag>
  <pat:InventionTitleBag>
   <pat:InventionTitle com:languageCode="cs" pat:inventionTitleCategory="In grant publication">Zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením</pat:InventionTitle>
   <pat:InventionTitle com:languageCode="en" pat:inventionTitleCategory="In grant publication">An equipment to connect photovoltaic panels to a distribution network with a backup power supply</pat:InventionTitle>
  </pat:InventionTitleBag>
  <pat:ClaimTotalQuantity>6</pat:ClaimTotalQuantity>
  <pat:PartyBag>
   <pat:ApplicantBag>
    <pat:Applicant>
     <com:Contact>
      <com:Name>
       <com:OrganizationName>
        <com:OrganizationStandardName>BENEKOV ESCO s.r.o.</com:OrganizationStandardName>
       </com:OrganizationName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Horní Benešov</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:Applicant>
   </pat:ApplicantBag>
   <pat:InventorBag>
    <pat:Inventor>
     <com:Contact>
      <com:Name>
       <com:PersonName>
        <com:PersonFullName>anonymizováno/anonymized</com:PersonFullName>
       </com:PersonName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Horní Benešov</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:Inventor>
   </pat:InventorBag>
   <pat:RegisteredPractitionerBag>
    <pat:RegisteredPractitioner com:sequenceNumber="1">
     <pat:RegisteredPractitionerCategory>Agent</pat:RegisteredPractitionerCategory>
     <com:Contact>
      <com:Name>
       <com:OrganizationName>
        <com:OrganizationStandardName>Ing. Pavel Nádvorník s.r.o.</com:OrganizationStandardName>
       </com:OrganizationName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Ostrava, Hulváky</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:RegisteredPractitioner>
   </pat:RegisteredPractitionerBag>
  </pat:PartyBag>
  <com:FilingLanguageCode>cs</com:FilingLanguageCode>
  <com:PublicationLanguageCode>cs</com:PublicationLanguageCode>
 </pat:BibliographicData>
 <pat:Description xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0" com:id="desc" com:languageCode="cs">
  <com:P com:pNumber="1">
   <com:B>Zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením</com:B>
  </com:P>
  <com:P com:pNumber="2"> </com:P>
  <com:P com:pNumber="3"> </com:P>
  <com:P com:pNumber="4">Oblast techniky  </com:P>
  <com:P com:pNumber="5"> </com:P>
  <com:P com:pNumber="6">Technické řešení se týká zařízení pro fotovoltaickou elektrárnu k připojení fotovoltaických panelů k elektrické distribuční síti. Zařízení je vybaveno integrovaným záložním napájením. Zařízení umožňuje nepřerušený provoz připojené fotovoltaické elektrárny i v případě výpadku distribuční sítě nebo jejího nestandardního napětí díky integrovaným akumulátorovým článkům.  </com:P>
  <com:P com:pNumber="7"> </com:P>
  <com:P com:pNumber="8"> </com:P>
  <com:P com:pNumber="9">Dosavadní stav techniky </com:P>
  <com:P com:pNumber="10"> </com:P>
  <com:P com:pNumber="11">Dosud známá zařízení pro připojení fotovoltaických panelů k distribuční síti jsou tvořena měničem, který je zejména u fotovoltaických elektráren o větším výkonu napájen přímo z distribuční sítě, resp. je k distribuční síti připojeno jeho ovládání tak, že reaguje na existenci napětí a jeho jmenovitý stav. </com:P>
  <com:P com:pNumber="12"> </com:P>
  <com:P com:pNumber="13">Typickým problémem běžných síťových střídačů pro fotovoltaické systémy je jejich neschopnost fungovat při jakémkoliv výpadku sítě, jejím přepětím či podpětím. </com:P>
  <com:P com:pNumber="14"> </com:P>
  <com:P com:pNumber="15"> </com:P>
  <com:P com:pNumber="16">Podstata technického řešení </com:P>
  <com:P com:pNumber="17"> </com:P>
  <com:P com:pNumber="18">Uvedené nevýhody odstraňuje zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením podle tohoto technického řešení.  </com:P>
  <com:P com:pNumber="19"> </com:P>
  <com:P com:pNumber="20">Zařízení zahrnuje měnič, AC rozvaděč, ovládací modul, síťovou ochranu, bateriový napěťový záložní zdroj obsahující dobíjecí baterii, automatický nabíječ a DC/AC převodník. </com:P>
  <com:P com:pNumber="21"> </com:P>
  <com:P com:pNumber="22">Měnič je svým vstupem připojitelný přes DC rozvaděč na fotovoltaické panely. Výstup měniče je připojitelný na distribuční síť. Připojení je realizováno přes AC rozvaděč, který je fotovoltaickým panelům předřazen. </com:P>
  <com:P com:pNumber="23">Součástí zařízení je bateriový napěťový záložní zdroj. Záložní zdroj obsahuje dobíjecí baterii, automatický nabíječ a DC/AC převodník. </com:P>
  <com:P com:pNumber="24"> </com:P>
  <com:P com:pNumber="25">Dobíjecí baterie je připojena na AC rozvaděč. Přitom zapojení dobíjecí baterie na AC rozvaděč je provedeno tak, že je na něj připojena jedním pólem přes DC/AC rozvaděč, síťovou ochranu a ovládací modul a druhým pólem přes automatický nabíječ.  </com:P>
  <com:P com:pNumber="26"> </com:P>
  <com:P com:pNumber="27">Výhodné je, pokud zařízení zahrnuje komunikační modul, který je propojený s výstupem měniče. Přitom komunikační modul je určen pro ovládání spínače spotřebičů přebytků elektrické energie vytvořené fotovoltaickými panely. </com:P>
  <com:P com:pNumber="28"> </com:P>
  <com:P com:pNumber="29">Výhodné je, pokud je AC rozvaděč opatřen výstupem pro připojení záložního okruhu. Na záložní okruh je připojen měnič. Záložní okruh je schopen provozu z fotovoltaické elektrárny v případě výpadku dodávek elektrické energie z distribuční sítě. </com:P>
  <com:P com:pNumber="30"> </com:P>
  <com:P com:pNumber="31">Výhodné je, pokud je zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením opatřeno připojením pro napojení bateriového úložiště, které slouží pro akumulaci elektrické energie z fotovoltaických panelů. </com:P>
  <com:P com:pNumber="32"> </com:P>
  <com:P com:pNumber="33">Je výhodné, pokud jsou všechny části zařízení, sloužící k připojení fotovoltaických panelů k distribuční síti se záložním napájením, integrovány do jednoho celku, který je umístěn v samostatném krytu. </com:P>
  <com:P com:pNumber="34"> </com:P>
  <com:P com:pNumber="35">Všechny prvky zařízení, vyznačené na přiložených výkresech čárkovaným obdélníkem, jsou kompletně uzavřeny v jednom krytu a tvoří jeden kompaktní výrobek. </com:P>
  <com:P com:pNumber="36"> </com:P>
  <com:P com:pNumber="37">Ostatní prvky zobrazené mimo čárkovaný obdélník na výkresech nejsou součástí zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením. Zařízení je však uzpůsobeno pro jejich napojení, a proto jsou k tomuto zařízení připojitelné. </com:P>
  <com:P com:pNumber="38"> </com:P>
  <com:P com:pNumber="39"> </com:P>
  <com:P com:pNumber="40">Objasnění výkresů </com:P>
  <com:P com:pNumber="41"> </com:P>
  <com:P com:pNumber="42">Technické řešení je blíže objasněno pomocí výkresů, na kterých je předloženo blokové schéma zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením, podle tohoto technického řešení. </com:P>
  <com:P com:pNumber="43"> </com:P>
  <com:P com:pNumber="44">Na obr. 1 je schéma zapojení zařízení v základním provedení podle nároku č.1. </com:P>
  <com:P com:pNumber="45">Na obr. 2 je schéma zapojení zařízení ve výhodném provedení, kdy je k němu připojeno bateriové úložiště. </com:P>
  <com:P com:pNumber="46">Na obr. 3 je schéma zapojení zařízení ve výhodném provedení, kdy je jeho součástí komunikační modul. K zařízení je připojeno bateriové úložiště a záložní okruh. </com:P>
  <com:P com:pNumber="47"> </com:P>
  <com:P com:pNumber="48"> </com:P>
  <com:P com:pNumber="49">Příklady uskutečnění technického řešení </com:P>
  <com:P com:pNumber="50"> </com:P>
  <com:P com:pNumber="51">V prvním příkladu uskutečnění technického řešení je rozhodnuto realizovat zařízení pro připojení fotovoltaických panelů 3 k distribuční síti 4 se záložním napájením, v základním provedení, které je zobrazeno na obr. 1. </com:P>
  <com:P com:pNumber="52">K jeho realizaci jsou použity následující prvky: </com:P>
  <com:P com:pNumber="53">Měnič 1, kterým je asymetrický, nízkonapěťový měnič model DEYE SUN20K-SG05LP3-EU-          -SM2 o jmenovitém výkonu 20 kW. </com:P>
  <com:P com:pNumber="54">Ovládací modul 5 je od výrobce TOMNZ. Obsahuje stykače rozpadového místa 25 A. Dále obsahuje nouzový vypínač při překročení proudu 25 A.  </com:P>
  <com:P com:pNumber="55">Síťová ochrana 13, obsahující prvky pro ochranu měniče 1 před nestandardními vlivy distribuční sítě 4. Měří v rozsahu napětí od 0 do 320 V. Výrobek je od firmy EsiT UF300. </com:P>
  <com:P com:pNumber="56">Záložní zdroj je tvořen třemi dílčími prvky: automatickým nabíječem 11, dobíjecí baterií 10 a DC/AC převodníkem 12. </com:P>
  <com:P com:pNumber="57">Automatický nabíječ 11 pro nabíjení dobíjecí baterie 10 je modul DD30CRTA. </com:P>
  <com:P com:pNumber="58">Dobíjecí baterie 10 je realizována modelem MGB VRLA AGM. Dobíjecí baterie 10 je o napětí 12 V při kapacitě 1,3 Ah. </com:P>
  <com:P com:pNumber="59">V zařízení je použit DC/AC převodník 12, který je realizován modelem Phoenix VE.Direct 250VA 12 V.  </com:P>
  <com:P com:pNumber="60">AC rozvaděč 2 obsahuje AC jištění 16 A. Dále obsahuje přepěťové ochrany T1+T2 do 375 V od výrobce TOMNZ. AC rozvaděč 2 je opatřen výstupem pro připojení záložního okruhu 14. Záložní okruh 14 je k AC rozvaděči 2 připojen. AC rozvaděč 2 je opatřen výstupem na připojení k distribuční síti 4.  </com:P>
  <com:P com:pNumber="61">Zařízení je takto na distribuční síť 4 připojeno. </com:P>
  <com:P com:pNumber="62"> </com:P>
  <com:P com:pNumber="63">Měnič 1 je opatřen vstupem pro připojení DC rozvaděče 6, na který jsou připojeny fotovoltaické panely 3. Fotovoltaické panely 3 jsou na vstup měniče 1 přes DC rozvaděč 6 připojeny. </com:P>
  <com:P com:pNumber="64">
   <com:B> </com:B>
  </com:P>
  <com:P com:pNumber="65">Funkce zařízení podle prvního příkladu uskutečnění technického řešení je následující: </com:P>
  <com:P com:pNumber="66">Fotovoltaické panely 3 přeměňují známým způsobem sluneční záření na elektrickou energii stejnosměrného napětí. V měniči 1 se převádí napětí z fotovoltaických panelů 3 na napětí distribuční sítě 4, tj. na střídavé napětí 230 V. Protože je realizováno připojení na distribuční síť 4, provede měnič 1 fázování napětí na frekvenci distribuční sítě 4. </com:P>
  <com:P com:pNumber="67"> </com:P>
  <com:P com:pNumber="68">V příkladném uskutečnění technického řešení je provedeno přifázování a elektrická energie odchází z měniče 1 přes AC rozvaděč 2 do distribuční sítě 4. </com:P>
  <com:P com:pNumber="69"> </com:P>
  <com:P com:pNumber="70">V AC rozváděči 2 je přepěťová ochrana, zabezpečující nepřekročení napětí přicházející do distribuční sítě 4. </com:P>
  <com:P com:pNumber="71">V případě výpadku napětí v distribuční síti 4 dochází u stávajících zařízení z technických i legislativních důvodů k odpojení fotovoltaické elektrárny. Odpojení je provedeno střídačem, kterým jsou stávající zařízení vybavena a jehož řídící obvody jsou připojeny na napětí distribuční sítě 4. Napětím distribuční sítě 4 je takto střídač ovládán. </com:P>
  <com:P com:pNumber="72">Stejným způsobem reaguje u stávajících zařízení střídač, pokud dojde ke snížení napětí distribuční sítě 4 nebo k jeho zvýšení. Takováto napěťová anomálie dokáže pozastavit činnost fotovoltaické elektrárny, přičemž její následné spuštění je časově nepříjemné.
   
   <com:B> </com:B>
  </com:P>
  <com:P com:pNumber="73">Zejména je nebezpečná napěťová anomálie v distribuční síti 4, na kterou je připojena řada výkonných fotovoltaických elektráren, protože jejich okamžité a současné vypnutí i následné zapnutí může způsobit nebezpečí blackoutu distribuční sítě 4. </com:P>
  <com:P com:pNumber="74">Uvedené nebezpečí odpadá při použití zařízení pro připojení fotovoltaických panelů 3 k distribuční síti 4 se záložním zdrojem napájení podle tohoto technického řešení, protože v případě napěťové anomálie nebo krátkodobého vypnutí distribuční sítě 4 je měnič 1 napájen z  </com:P>
  <com:P com:pNumber="75">dobíjecí baterie 10 záložního zdroje. </com:P>
  <com:P com:pNumber="76"> </com:P>
  <com:P com:pNumber="77">Bateriový napěťový záložní zdroj obsahuje dobíjecí baterii 10, která je neustále udržována v nabitém stavu pomocí automatického nabíječe 11, na který je napojena. Napětí z dobíjecí baterie 10, které je stejnosměrné, je převáděno DC/AC převodníkem 12 na napětí střídavé, které vyžadují vstupy řídících obvodů měniče 1, uzpůsobené na střídavé napětí distribuční sítě 4. Střídavé napětí z dobíjecí baterie 10 se k obvodům měniče 1 dostává přes AC rozvaděč 2.  </com:P>
  <com:P com:pNumber="78">AC rozvaděč 2 rovněž zabezpečuje svou přepěťovou ochranou, že nedojde k překročení nominálního napětí o předem nastavenou mez.  </com:P>
  <com:P com:pNumber="79"> </com:P>
  <com:P com:pNumber="80">Ve druhém příkladu uskutečnění technického řešení je rozhodnuto realizovat zařízení pro připojení fotovoltaických panelů 3 k distribuční síti 4 se záložním napájením v provedení, které je zobrazeno na obr. 2. </com:P>
  <com:P com:pNumber="81">K jeho realizaci jsou použity stejné prvky jako v prvním příkladu uskutečnění. Zařízení pro připojení fotovoltaických panelů 3 je však doplněno o možnost připojení bateriového úložiště 9 tím, že měnič 1 je hybridní a je opatřen vstupem pro připojení bateriového úložiště 9. </com:P>
  <com:P com:pNumber="82">Měnič 1 je uzpůsoben pro komunikaci s bateriovým úložištěm 9 a k jeho řízení.  </com:P>
  <com:P com:pNumber="83">Bateriové úložiště 9 je tvořeno pěti bateriovými moduly BENEKOV BATERIX 5K, každý o nominální kapacitě 5 kWh. Celková kapacita je 25 kWh. </com:P>
  <com:P com:pNumber="84"> </com:P>
  <com:P com:pNumber="85">Ve druhém příkladném uskutečnění je bateriové úložiště 9 na zařízení připojeno. </com:P>
  <com:P com:pNumber="86"> </com:P>
  <com:P com:pNumber="87">Funkce zařízení podle druhého příkladu uskutečnění technického řešení je vůči prvnímu příkladu uskutečnění rozšířena tím, že je na měnič 1 napojeno bateriové úložiště 9. Dochází tak známým způsobem k jeho nabíjení a v případě potřeby k použití takto uskladněné elektrické energie. Přitom nabíjení a vybíjení bateriového úložiště 9 řídí měnič 1, který je v tom případě hybridní. </com:P>
  <com:P com:pNumber="88">  </com:P>
  <com:P com:pNumber="89">Ve třetím příkladu uskutečnění technického řešení je rozhodnuto realizovat zařízení pro připojení fotovoltaických panelů 3 k distribuční síti 4 se záložním napájením v provedení, které je zobrazeno na obr. 3. </com:P>
  <com:P com:pNumber="90"> </com:P>
  <com:P com:pNumber="91">K jeho realizaci jsou použity stejné prvky jako v druhém příkladu uskutečnění. Zařízení pro připojení fotovoltaických panelů 3 je však doplněno o možnost připojení záložního okruhu 14 a možnost ovládání spotřebičů 8 přebytků elektrické energie pomocí komunikačního modulu 15 přes spínač 7. </com:P>
  <com:P com:pNumber="92"> </com:P>
  <com:P com:pNumber="93">Proto je měnič 1 zařízení pro připojení fotovoltaických panelů 3 k distribuční síti 4 se záložním napájením opatřen výstupem pro připojení komunikačního modulu 15 pro ovládání spínače 7 spotřebičů 8 přebytků elektrické energie.  </com:P>
  <com:P com:pNumber="94">Komunikačním modulem 15 je model IBeeM V 3.1. od výrobce BENEKOVterm. Komunikační modul 15 je k měniči 1 připojen. </com:P>
  <com:P com:pNumber="95">Spotřebičem 8 přebytků elektrické energie je bojler pro teplou užitkovou vodu s kapacitou 200 litrů. Je použit typ OKCE200 od výrobce Dražice. Tento spotřebič 8 přebytků elektrické energie je přes spínač 7 připojen k distribuční síti 4. Spínač 7 je ovládán komunikačním modulem 15. </com:P>
  <com:P com:pNumber="96"> </com:P>
  <com:P com:pNumber="97">Funkce zařízení podle třetího příkladu uskutečnění technického řešení je obdobná s funkcí podle druhého příkladu uskutečnění. Je však rozšířena o činnost záložního okruhu 14. </com:P>
  <com:P com:pNumber="98">Záložním okruhem 14 je zálohovaný okruh, na který je napojen měnič 1. Tento okruh 14 je schopen provozu z fotovoltaické elektrárny v případě výpadku dodávek elektrické energie z distribuční sítě 4. </com:P>
  <com:P com:pNumber="99"> </com:P>
  <com:P com:pNumber="100">Funkce zařízení podle třetího příkladu uskutečnění technického řešení je rovněž rozšířena o činnost komunikačního modulu 15.  </com:P>
  <com:P com:pNumber="101"> </com:P>
  <com:P com:pNumber="102">Komunikační modul 15 je napojen na měnič 1 a umožňuje pomocí spínače 7 distribuovat proud do vybraných spotřebičů 8, které jsou zapojeny do distribuční sítě 4. Pro realizaci je použit model IBeeM V 3.1. od výrobce BENEKOVterm. </com:P>
  <com:P com:pNumber="103">Komunikační modul 15 umožnuje ovládání spínače 7 a tímto spínačem 7 zapínání a vypínání spotřebičů 8 přebytků elektrické energie v případě, že fotovoltaické panely 3 vyrábějí přebytek elektrické energie. Takto využitá elektrická energie je ekonomický výhodnější, nežli její prodej do distribuční sítě 4. </com:P>
  <com:P com:pNumber="104">Přebytek elektrické energie z fotovoltaických panelů 3 je v tomto příkladě uskutečnění použit </com:P>
  <com:P com:pNumber="105">pro ohřev teplé užitkové vody v spotřebiči 8 přebytků elektrické energie, kterým je bojler TUV.  </com:P>
  <com:P com:pNumber="106"> </com:P>
  <com:P com:pNumber="107"> </com:P>
  <com:P com:pNumber="108">Průmyslová využitelnost </com:P>
  <com:P com:pNumber="109"> </com:P>
  <com:P com:pNumber="110">Zařízení zvyšuje bezpečnost provozu elektrické distribuční sítě, protože zařízení pro připojení fotovoltaických panelů k distribuční síti se záložním napájením nepodléhá výpadkům provozu při nestandardních stavech této distribuční sítě. Zařízení je vhodné zejména, pokud je potřeba udržovat zvýšenou stabilitu distribuční sítě, například tam, kde se nachází prvky kritické infrastruktury, například pro nemocnice, záchrannou službu a prvky občanské vybavenosti. </com:P>
  <pat:DrawingDescription>
   <com:P>     1 - měnič
    
    <com:Br></com:Br>     2 - AC rozvaděč
    
    <com:Br></com:Br>     3 - fotovoltaické panely
    
    <com:Br></com:Br>     4 - distribuční síť
    
    <com:Br></com:Br>     5 - ovládací modul
    
    <com:Br></com:Br>     6 - DC rozvaděč
    
    <com:Br></com:Br>     7 - spínač
    
    <com:Br></com:Br>     8 - spotřebič přebytků elektrické energie
    
    <com:Br></com:Br>     9 - bateriové úložiště
    
    <com:Br></com:Br>    10 - dobíjecí baterie
    
    <com:Br></com:Br>    11 - automatický nabíječ
    
    <com:Br></com:Br>    12 - DC/AC převodník
    
    <com:Br></com:Br>    13 - sítová ochrana
    
    <com:Br></com:Br>    14 - záložní okruh
    
    <com:Br></com:Br>    15 - komunikační modul
   
   </com:P>
  </pat:DrawingDescription>
 </pat:Description>
 <pat:Claims xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0">
  <pat:Claim>
   <pat:ClaimNumber>1</pat:ClaimNumber>
   <pat:ClaimText>Zařízení pro připojení fotovoltaických panelů (3) k distribuční síti (4) se záložním napájením, 
    
    <com:B>vyznačující se tím</com:B>, že zahrnuje:- měnič (1)- AC rozvaděč (2),- ovládací modul (5),- síťovou ochranu (13),- bateriový napěťový záložní zdroj obsahující dobíjecí baterii (10), automatický nabíječ (11) a DC/AC převodník (12),přičemž měnič (1) je svým vstupem připojitelný přes DC rozvaděč (6) na fotovoltaické panely (3) a svým výstupem přes AC rozvaděč (2) na distribuční síť (4),přičemž dobíjecí baterie (10) záložního zdroje je na AC rozvaděč (2) napojená:- jedním pólem přes DC/AC převodník (12), síťovou ochranu (13) a ovládací modul (5),- druhým pólem přes automatický nabíječ (11).
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>2</pat:ClaimNumber>
   <pat:ClaimText>Zařízení pro připojení fotovoltaických panelů (3) k distribuční síti (4) se záložním napájením, 
    
    <com:B>vyznačující se tím</com:B>,
    
    <com:B> </com:B>že zahrnuje:- měnič (1)- AC rozvaděč (2),- ovládací modul (5),- síťovou ochranu (13),- bateriový napěťový záložní zdroj obsahující dobíjecí baterii (10), automatický nabíječ (11) a DC/AC převodník (12),přičemž měnič (1) je svým vstupem připojitelný přes DC rozvaděč (6) na fotovoltaické panely (3) a svým výstupem přes AC rozvaděč (2) na distribuční síť (4),přičemž dobíjecí baterie (10) záložního zdroje je na AC rozvaděč (2) napojená:- jedním pólem přes DC/AC převodník (12), síťovou ochranu (13) a ovládací modul (5),- druhým pólem přes automatický nabíječ (11),přičemž AC rozvaděč (2) je opatřen výstupem pro připojení záložního okruhu (14).
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>3</pat:ClaimNumber>
   <pat:ClaimText>Zařízení pro připojení fotovoltaických panelů (3) k distribuční síti (4) se záložním napájením, 
    
    <com:B>vyznačující se tím</com:B>, že zahrnuje:- měnič (1)- AC rozvaděč (2),- ovládací modul (5),- síťovou ochranu (13),- bateriový napěťový záložní zdroj obsahující dobíjecí baterii (10), automatický nabíječ (11) a DC/AC převodník (12),přičemž měnič (1) je svým vstupem připojitelný přes DC rozvaděč (6) na fotovoltaické panely (3) a svým výstupem přes AC rozvaděč (2) na distribuční síť (4),přičemž dobíjecí baterie (10) záložního zdroje je na AC rozvaděč (2) napojená:- jedním pólem přes DC/AC převodník (12), síťovou ochranu (13) a ovládací modul (5),- druhým pólem přes automatický nabíječ (11),přičemž měnič (1) je opatřen vstupem pro připojení bateriového úložiště (9) a je uzpůsoben pro komunikaci s bateriovým úložištěm (9) a k jeho řízení.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>4</pat:ClaimNumber>
   <pat:ClaimText>Zařízení pro připojení fotovoltaických panelů (3) k distribuční síti (4) se záložním napájením, 
    
    <com:B>vyznačující se tím</com:B>, že zahrnuje:- měnič (1)- AC rozvaděč (2),- ovládací modul (5),- síťovou ochranu (13),- bateriový napěťový záložní zdroj obsahující dobíjecí baterii (10), automatický nabíječ (11) a DC/AC převodník (12),přičemž měnič (1) je svým vstupem připojitelný přes DC rozvaděč (6) na fotovoltaické panely (3) a svým výstupem přes AC rozvaděč (2) na distribuční síť (4),přičemž dobíjecí baterie (10) záložního zdroje je na AC rozvaděč (2) napojená:- jedním pólem přes DC/AC převodník (12), síťovou ochranu (13) a ovládací modul (5),- druhým pólem přes automatický nabíječ (11),přičemž AC rozvaděč (2) je opatřen výstupem pro připojení záložního okruhu (14),přičemž měnič (1) je opatřen připojením pro napojení bateriového úložiště (9) a je uzpůsoben pro komunikaci s bateriovým úložištěm (9) a k jeho řízení.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>5</pat:ClaimNumber>
   <pat:ClaimText>Zařízení pro připojení fotovoltaických panelů (3) k distribuční síti (4) se záložním napájením, 
    
    <com:B>vyznačující se tím</com:B>, že zahrnuje:- měnič (1)- AC rozvaděč (2),- ovládací modul (5),- síťovou ochranu (13),- bateriový napěťový záložní zdroj obsahující dobíjecí baterii (10), automatický nabíječ (11) a DC/AC převodník (12),přičemž měnič (1) je svým vstupem připojitelný přes DC rozvaděč (6) na fotovoltaické panely (3) a svým výstupem přes AC rozvaděč (2) na distribuční síť (4),přičemž dobíjecí baterie (10) záložního zdroje je na AC rozvaděč (2) napojená:- jedním pólem přes DC/AC převodník (12), síťovou ochranu (13) a ovládací modul (5),- druhým pólem přes automatický nabíječ (11),přičemž zahrnuje komunikační modul (15), určený pro ovládání spínače (7) spotřebičů (8) přebytků elektrické energie vytvořené fotovoltaickými panely (3), přičemž komunikační modul (15) je propojen s měničem (1).
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>6</pat:ClaimNumber>
   <pat:ClaimText>Zařízení podle kteréhokoliv z předchozích nároků, 
    
    <com:B>vyznačující se tím</com:B>, že tvoří jeden celek umístěný v jednom krytu.
   
   </pat:ClaimText>
  </pat:Claim>
 </pat:Claims>
 <pat:Drawings xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0">
  <pat:Figure>
   <pat:FigureNumber>1</pat:FigureNumber>
   <com:Image com:id="img-1" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2611489img0001.jpg</com:FileName>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>2</pat:FigureNumber>
   <com:Image com:id="img-2" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2611489img0002.jpg</com:FileName>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>3</pat:FigureNumber>
   <com:Image com:id="img-3" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2611489img0003.jpg</com:FileName>
   </com:Image>
  </pat:Figure>
 </pat:Drawings>
</pat:PatentPublication>