
<pat:PatentPublication xmlns:pat="http://www.wipo.int/standards/XMLSchema/ST96/Patent" xmlns:xsi="http://www.w3.org/2001/XMLSchema-instance" xmlns:com="http://www.wipo.int/standards/XMLSchema/ST96/Common" com:st96Version="V7_0" com:documentFileName="OPENDATAST96_PT_CZ_DIFF_PV2025-590.xml" com:languageCode="cs" xsi:schemaLocation="http://www.wipo.int/standards/XMLSchema/ST96/Patent https://isdv.upv.gov.cz/doc/xsd/ST96/PatentPublication_V7_0.xsd">
 <com:IPOfficeCode>CS</com:IPOfficeCode>
 <pat:BibliographicData com:st96Version="V7_0" com:officeCode="CZ">
  <pat:PatentPublicationIdentification>
   <com:IPOfficeCode>CZ</com:IPOfficeCode>
   <pat:PublicationNumber>2025-590</pat:PublicationNumber>
   <com:PatentDocumentKindCode>A3</com:PatentDocumentKindCode>
   <com:PublicationDate>2026-03-18</com:PublicationDate>
  </pat:PatentPublicationIdentification>
  <pat:ApplicationIdentification>
   <com:IPOfficeCode>CZ</com:IPOfficeCode>
   <com:ApplicationNumber>
    <com:ApplicationNumberText>2025-590</com:ApplicationNumberText>
   </com:ApplicationNumber>
   <com:FilingLanguageCode>cs</com:FilingLanguageCode>
   <pat:ApplicationFilingCategory>National</pat:ApplicationFilingCategory>
   <pat:FilingDate>2025-12-16</pat:FilingDate>
  </pat:ApplicationIdentification>
  <pat:PriorityClaimBag>
   <pat:PriorityClaim com:sequenceNumber="1">
    <com:IPOfficeCode>CZ</com:IPOfficeCode>
    <pat:FilingDate>2025-12-16</pat:FilingDate>
    <pat:ApplicationFilingCategory>National</pat:ApplicationFilingCategory>
   </pat:PriorityClaim>
  </pat:PriorityClaimBag>
  <pat:PatentClassificationBag>
   <pat:CPCClassificationBag>
    <pat:MainCPC>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20141201</pat:ClassificationVersionDate>
      <pat:CPCSection>H</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>S</pat:Subclass>
      <pat:MainGroup>40</pat:MainGroup>
      <pat:Subgroup>38</pat:Subgroup>
      <com:SymbolPositionCode>F</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>I</pat:CPCClassificationValueCode>
      <pat:ActionDate>20260225</pat:ActionDate>
      <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
    </pat:MainCPC>
    <pat:FurtherCPC>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20141201</pat:ClassificationVersionDate>
      <pat:CPCSection>H</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>S</pat:Subclass>
      <pat:MainGroup>40</pat:MainGroup>
      <pat:Subgroup>34</pat:Subgroup>
      <com:SymbolPositionCode>L</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>I</pat:CPCClassificationValueCode>
      <pat:ActionDate>20260225</pat:ActionDate>
      <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20141201</pat:ClassificationVersionDate>
      <pat:CPCSection>H</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>S</pat:Subclass>
      <pat:MainGroup>40</pat:MainGroup>
      <pat:Subgroup>32</pat:Subgroup>
      <com:SymbolPositionCode>L</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>I</pat:CPCClassificationValueCode>
      <pat:ActionDate>20260225</pat:ActionDate>
      <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20130101</pat:ClassificationVersionDate>
      <pat:CPCSection>Y</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>E</pat:Subclass>
      <pat:MainGroup>10</pat:MainGroup>
      <pat:Subgroup>56</pat:Subgroup>
      <com:SymbolPositionCode>L</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>A</pat:CPCClassificationValueCode>
      <pat:ActionDate>20260323</pat:ActionDate>
      <pat:GeneratingOfficeCode>EP</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>G</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
     <pat:CPCClassification>
      <pat:ClassificationVersionDate>20130101</pat:ClassificationVersionDate>
      <pat:CPCSection>Y</pat:CPCSection>
      <pat:Class>02</pat:Class>
      <pat:Subclass>B</pat:Subclass>
      <pat:MainGroup>10</pat:MainGroup>
      <pat:Subgroup>10</pat:Subgroup>
      <com:SymbolPositionCode>L</com:SymbolPositionCode>
      <pat:CPCClassificationValueCode>A</pat:CPCClassificationValueCode>
      <pat:ActionDate>20260323</pat:ActionDate>
      <pat:GeneratingOfficeCode>EP</pat:GeneratingOfficeCode>
      <pat:CPCClassificationStatusCode>B</pat:CPCClassificationStatusCode>
      <pat:PatentClassificationDataSourceCode>G</pat:PatentClassificationDataSourceCode>
     </pat:CPCClassification>
    </pat:FurtherCPC>
   </pat:CPCClassificationBag>
   <pat:IPCRClassificationBag>
    <pat:IPCRClassification com:sequenceNumber="1">
     <pat:ClassificationVersionDate>20140101</pat:ClassificationVersionDate>
     <pat:PatentClassificationLevelCode>A</pat:PatentClassificationLevelCode>
     <com:SymbolPositionCode>F</com:SymbolPositionCode>
     <pat:IPCClassificationValueCode>I</pat:IPCClassificationValueCode>
     <pat:ActionDate>20260225</pat:ActionDate>
     <pat:IPCClassificationStatusCode>B</pat:IPCClassificationStatusCode>
     <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
     <pat:Section>H</pat:Section>
     <pat:Class>02</pat:Class>
     <pat:Subclass>S</pat:Subclass>
     <pat:MainGroup>40</pat:MainGroup>
     <pat:Subgroup>38</pat:Subgroup>
    </pat:IPCRClassification>
    <pat:IPCRClassification com:sequenceNumber="2">
     <pat:ClassificationVersionDate>20140101</pat:ClassificationVersionDate>
     <pat:PatentClassificationLevelCode>A</pat:PatentClassificationLevelCode>
     <com:SymbolPositionCode>L</com:SymbolPositionCode>
     <pat:IPCClassificationValueCode>I</pat:IPCClassificationValueCode>
     <pat:ActionDate>20260225</pat:ActionDate>
     <pat:IPCClassificationStatusCode>B</pat:IPCClassificationStatusCode>
     <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
     <pat:Section>H</pat:Section>
     <pat:Class>02</pat:Class>
     <pat:Subclass>S</pat:Subclass>
     <pat:MainGroup>40</pat:MainGroup>
     <pat:Subgroup>34</pat:Subgroup>
    </pat:IPCRClassification>
    <pat:IPCRClassification com:sequenceNumber="3">
     <pat:ClassificationVersionDate>20140101</pat:ClassificationVersionDate>
     <pat:PatentClassificationLevelCode>A</pat:PatentClassificationLevelCode>
     <com:SymbolPositionCode>L</com:SymbolPositionCode>
     <pat:IPCClassificationValueCode>I</pat:IPCClassificationValueCode>
     <pat:ActionDate>20260225</pat:ActionDate>
     <pat:IPCClassificationStatusCode>B</pat:IPCClassificationStatusCode>
     <pat:PatentClassificationDataSourceCode>H</pat:PatentClassificationDataSourceCode>
     <pat:GeneratingOfficeCode>CZ</pat:GeneratingOfficeCode>
     <pat:Section>H</pat:Section>
     <pat:Class>02</pat:Class>
     <pat:Subclass>S</pat:Subclass>
     <pat:MainGroup>40</pat:MainGroup>
     <pat:Subgroup>32</pat:Subgroup>
    </pat:IPCRClassification>
   </pat:IPCRClassificationBag>
  </pat:PatentClassificationBag>
  <pat:InventionTitleBag>
   <pat:InventionTitle com:languageCode="cs" pat:inventionTitleCategory="In application published">Souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů, vhodná pro rodinný dům</pat:InventionTitle>
   <pat:InventionTitle com:languageCode="en" pat:inventionTitleCategory="In application published">A kit for the generation and accumulation of electric energy from photovoltaic panels, suitable for a detached house</pat:InventionTitle>
  </pat:InventionTitleBag>
  <pat:ClaimTotalQuantity>7</pat:ClaimTotalQuantity>
  <pat:PartyBag>
   <pat:ApplicantBag>
    <pat:Applicant>
     <com:Contact>
      <com:Name>
       <com:OrganizationName>
        <com:OrganizationStandardName>BENEKOV ESCO s.r.o.</com:OrganizationStandardName>
       </com:OrganizationName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Horní Benešov</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:Applicant>
   </pat:ApplicantBag>
   <pat:InventorBag>
    <pat:Inventor>
     <com:Contact>
      <com:Name>
       <com:PersonName>
        <com:PersonFullName>anonymizováno/anonymized</com:PersonFullName>
       </com:PersonName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Horní Benešov</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:Inventor>
   </pat:InventorBag>
   <pat:RegisteredPractitionerBag>
    <pat:RegisteredPractitioner com:sequenceNumber="1">
     <pat:RegisteredPractitionerCategory>Agent</pat:RegisteredPractitionerCategory>
     <com:Contact>
      <com:Name>
       <com:OrganizationName>
        <com:OrganizationStandardName>Ing. Pavel Nádvorník s.r.o.</com:OrganizationStandardName>
       </com:OrganizationName>
      </com:Name>
      <com:PostalAddressBag>
       <com:PostalAddress>
        <com:PostalStructuredAddress>
         <com:CityName>Ostrava, Hulváky</com:CityName>
         <com:CountryCode>CZ</com:CountryCode>
        </com:PostalStructuredAddress>
       </com:PostalAddress>
      </com:PostalAddressBag>
     </com:Contact>
    </pat:RegisteredPractitioner>
   </pat:RegisteredPractitionerBag>
  </pat:PartyBag>
  <com:FilingLanguageCode>cs</com:FilingLanguageCode>
  <com:PublicationLanguageCode>cs</com:PublicationLanguageCode>
 </pat:BibliographicData>
 <pat:Description xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0" com:id="desc" com:languageCode="cs">
  <com:P com:pNumber="1">
   <com:B>Souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů, vhodná pro rodinný dům</com:B>
  </com:P>
  <com:P com:pNumber="2"> </com:P>
  <com:P com:pNumber="3"> </com:P>
  <com:P com:pNumber="4">Oblast techniky </com:P>
  <com:P com:pNumber="5"> </com:P>
  <com:P com:pNumber="6">Vynález se týká soupravy pro výrobu a akumulaci elektrické energie z fotovoltaických panelů, která je vhodná pro menší budovu, zejména pro rodinný dům. </com:P>
  <com:P com:pNumber="7"> </com:P>
  <com:P com:pNumber="8"> </com:P>
  <com:P com:pNumber="9">Dosavadní stav techniky </com:P>
  <com:P com:pNumber="10"> </com:P>
  <com:P com:pNumber="11">Jsou známa různá technická řešení fotovoltaických elektráren, u kterých jsou fotovoltaické panely umístěny na střeše nebo v blízkosti budovy a vyrábějí elektrickou energii za účelem jejího přímého využití v budově, popřípadě pro nabíjení bateriového úložiště. </com:P>
  <com:P com:pNumber="12"> </com:P>
  <com:P com:pNumber="13">Fotovoltaické systémy používané v budovách mohou být uzpůsobeny prostřednictvím střídače pro připojení k veřejné síti. Obvykle jsou fotovoltaické panely těchto systémů instalované na střeše budovy. U rodinných domků je instalace fotovoltaických panelů téměř výhradně na střeše domu. Fotovoltaické panely mohou být umístěny rovněž na fasádách budovy nebo instalovány jako samostatné pozemní fotovoltaické systémy mimo samotnou stavbu.  </com:P>
  <com:P com:pNumber="14"> </com:P>
  <com:P com:pNumber="15">Výstup fotovoltaických panelů je obvykle připojen ke střídači, který zajišťuje konverzi stejnosměrného napětí na napětí střídavé a zprostředkovává dodávku elektrické energie do distribuční sítě nebo do vnitřní elektrické instalace nemovitosti. </com:P>
  <com:P com:pNumber="16"> </com:P>
  <com:P com:pNumber="17">Fotovoltaické panely jsou běžně zapojovány sériově nebo sérioparalelně, aby bylo dosaženo vyšších stejnosměrných napětí, které mnohdy přesahují 300 až 800 V DC. Vyšší napětí zapojení přispívá k vyšší energetické účinnosti systému, neboť elektronické prvky při vyšším napětí vykazují nižší výkonové ztráty. </com:P>
  <com:P com:pNumber="18"> </com:P>
  <com:P com:pNumber="19">Vysoké napětí v oblasti fotovoltaických panelů představuje významnou nevýhodu vzhledem ke zvýšenému riziku úrazu elektrickým proudem při náhodném kontaktu s částmi fotovoltaické elektrárny, které jsou pod tímto napětím. Riziko je obzvlášť závažné při montáži a údržbě zařízení, kdy osoby přicházejí do blízkosti elektricky vodivých částí systému. </com:P>
  <com:P com:pNumber="20"> </com:P>
  <com:P com:pNumber="21">Vyšší napětí je rovněž nevýhodné v případě požáru budovy, kdy je nutné řešit technické i legislativní požadavky na zajištění bezpečnosti zasahujících hasičů. Možnosti bezpečného odpojení jednotlivých sekcí fotovoltaického pole při údržbě, poruše nebo požáru jsou přitom omezené, a ne vždy plně bezpečné. </com:P>
  <com:P com:pNumber="22"> </com:P>
  <com:P com:pNumber="23">Další nevýhodou současných řešení je nízká modularita zapojení, což je problém zejména tam, kde je požadována flexibilita nebo možnost rozšiřování fotovoltaického systému. V praxi to může znamenat, že není snadné přidat další část instalace, nahradit rozhraní nebo změnit konfiguraci bez zásahu do celého zařízení. </com:P>
  <com:P com:pNumber="24"> </com:P>
  <com:P com:pNumber="25">Současné systémy také zpravidla vyžadují použití vysoce specializovaných komponentů, což zvyšuje jejich pořizovací i servisní náklady a může komplikovat instalaci v prostorově omezených podmínkách. </com:P>
  <com:P com:pNumber="26"> </com:P>
  <com:P com:pNumber="27"> </com:P>
  <com:P com:pNumber="28">Podstata vynálezu </com:P>
  <com:P com:pNumber="29"> </com:P>
  <com:P com:pNumber="30">Uvedené nevýhody odstraňuje souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů, vhodná pro menší budovu, zejména pro rodinný dům. </com:P>
  <com:P com:pNumber="31"> </com:P>
  <com:P com:pNumber="32">Vynález je určen pro menší budovu, jejíž odběrná místa jsou propojena vnitřním elektrickým rozvodem, který je napojený přes distribuční elektroměr na distribuční síť. </com:P>
  <com:P com:pNumber="33"> </com:P>
  <com:P com:pNumber="34">Pro svou jednoduchost je vynález vhodný pro použití pro rodinný dům. </com:P>
  <com:P com:pNumber="35"> </com:P>
  <com:P com:pNumber="36">Vynález zahrnuje: </com:P>
  <com:P com:pNumber="37"> </com:P>
  <com:P com:pNumber="38">- fotovoltaické panely,  </com:P>
  <com:P com:pNumber="39">- mikrostřídače, </com:P>
  <com:P com:pNumber="40">- hybridní měnič,   </com:P>
  <com:P com:pNumber="41">- bateriové úložiště, </com:P>
  <com:P com:pNumber="42">- signální vedení. </com:P>
  <com:P com:pNumber="43"> </com:P>
  <com:P com:pNumber="44">Každý fotovoltaický panel, který je použit pro vynález, má jmenovité napětí menší než 120 V, což znamená, že žádný fotovoltaický panel není schopen vytvořit vlivem působení jakkoliv intenzivního světelného toku napětí, které by dosáhlo nebo překročilo 120 V DC. </com:P>
  <com:P com:pNumber="45"> </com:P>
  <com:P com:pNumber="46">Podstatné je, že každý mikrostřídač je opatřen jedním až šesti vstupy. Ke každému mikrostřídači je připojen alespoň jeden a nejvýše šest fotovoltaických panelů. Přitom na žádný vstup mikrostřídači není připojen více než jeden fotovoltaický panel. </com:P>
  <com:P com:pNumber="47"> </com:P>
  <com:P com:pNumber="48">Výstupy všech mikrostřídačů jsou napojitelné na vnitřní elektrický rozvod budovy. </com:P>
  <com:P com:pNumber="49"> </com:P>
  <com:P com:pNumber="50">Na vnitřní elektrický rozvod budovy je rovněž napojitelný hybridní měnič, na který je napojeno bateriové úložiště. Bateriové úložiště má výstupní napětí nižší než 120 V DC. Znamená to, že mezi kterýmikoliv dvěmi body bateriového úložiště je vždy napětí nižší než 120 V DC. </com:P>
  <com:P com:pNumber="51"> </com:P>
  <com:P com:pNumber="52">Aby bylo možné získat informace o velikosti a směru proudu procházejícího přes distribuční elektroměr, je hybridní měnič připojitelný pomocí signálního vedení k distribučnímu elektroměru. </com:P>
  <com:P com:pNumber="53"> </com:P>
  <com:P com:pNumber="54">Mnohdy však nelze připojit hybridní měnič k distribučnímu elektroměru, protože distribuční elektroměr je ve vlastnictví distributora elektrické energie a není dovoleno do něj zasahovat. Pro tento případ je součástí zařízení podle tohoto vynálezu podružný elektroměr, který je určen pro zapojení mezi distribuční elektroměr a vnitřní elektrický rozvod budovy. </com:P>
  <com:P com:pNumber="55"> </com:P>
  <com:P com:pNumber="56">V takovém případě se informace o velikosti a směru proudu procházejícího distribučním elektroměrem získávají z uvedeného sériově zapojeného podružného elektroměru, k němuž je hybridní měnič připojen pomocí signálního vedení, jelikož proud procházející distribučním elektroměrem je totožný s proudem procházejícím tímto sériově zapojeným podružným elektroměrem. Podružný elektroměr je v tom případě určen k napojení na výstup distribučního elektroměru. </com:P>
  <com:P com:pNumber="57"> </com:P>
  <com:P com:pNumber="58">Výhodné je, pokud zařízení zahrnuje řídící a monitorovací jednotku, která je propojena s hybridním měničem a jednotlivými mikrostřídači. V tom případě řídící a monitorovací jednotka zahrnuje datové úložiště, mikropočítač s procesorem, operační paměť, analogové a/nebo digitální vstupy a analogové a/nebo digitální výstupy.  </com:P>
  <com:P com:pNumber="59"> </com:P>
  <com:P com:pNumber="60">Tato řídící a monitorovací jednotka je uzpůsobena pro: </com:P>
  <com:P com:pNumber="61"> </com:P>
  <com:P com:pNumber="62">- příjem a ukládání informací o aktuální výrobě fotovoltaických panelů získaných z jednotlivých mikrostřidačů;  </com:P>
  <com:P com:pNumber="63">- získávání a ukládání dat o provozních stavech hybridního měniče;  </com:P>
  <com:P com:pNumber="64">- zadávání instrukcí k provozu hybridního měniče;  </com:P>
  <com:P com:pNumber="65">- zadávání instrukcí k nabíjení a vybíjení bateriového úložiště přes hybridní měnič;  </com:P>
  <com:P com:pNumber="66">- rovněž pro příjem, zpracování a ukládání informací z bateriového úložiště, získaných z hybridního měniče. </com:P>
  <com:P com:pNumber="67"> </com:P>
  <com:P com:pNumber="68">V typickém provedení soupravy vhodné zejména pro rodinný dům má bateriové úložiště články zhotovené technologií LFP, popřípadě technologií LTO. </com:P>
  <com:P com:pNumber="69"> </com:P>
  <com:P com:pNumber="70">Pokud je v budově vnitřní elektrický rozvod 3fázový, je použit rovněž 3fázový hybridní měnič. </com:P>
  <com:P com:pNumber="71"> </com:P>
  <com:P com:pNumber="72">Hybridní měnič může být asymetrický. Znamená to, že hybridní měnič může být navržen tak, aby pracoval v asymetrickém režimu, což umožňuje optimalizovat jeho výkon a flexibilitu v závislosti na konkrétních provozních podmínkách a požadavcích systému. </com:P>
  <com:P com:pNumber="73"> </com:P>
  <com:P com:pNumber="74">Maximální DC napětí mezi jakýmikoliv dvěma DC body soupravy nikdy nedosáhne 120 V DC. To je zajištěno tím, že aktivní prvky, které generují nebo uchovávají napětí jsou provedeny s napětím nižším než 120 V DC. Jsou to fotovoltaické panely, které jsou pod 120 V DC a nejsou zapojeny v sérii a bateriové úložiště, které má napětí pod 120 V DC.  </com:P>
  <com:P com:pNumber="75"> </com:P>
  <com:P com:pNumber="76">Odběrným místem je pro účely tohoto vynálezu místo, ze kterého lze odebírat elektrickou energii standardních parametrů. Je to zásuvka, přívod pro elektrický bojler, elektrický přívod do bytové jednotky, přívod na světelný zdroj, přívod do garáže a podobně.  </com:P>
  <com:P com:pNumber="77"> </com:P>
  <com:P com:pNumber="78">Vnitřním elektrickým rozvodem budovy se pro účely tohoto vynálezu rozumí soubor vodičů, kabelů, rozvaděčů, jištění a dalších elektroinstalačních prvků umístěných uvnitř budovy, které zajišťují rozvod elektrické energie od hlavního domovního rozvaděče, ve které je umístěn distribuční elektroměr. </com:P>
  <com:P com:pNumber="79"> </com:P>
  <com:P com:pNumber="80">Realizace vynálezu má zejména tyto technické účinky: </com:P>
  <com:P com:pNumber="81"> </com:P>
  <com:P com:pNumber="82">- Fotvoltaika vyrábí elektřinu ze slunečního záření pomocí solárních panelů. </com:P>
  <com:P com:pNumber="83">- Výroba je z obnovitelného zdroje. </com:P>
  <com:P com:pNumber="84">- Výrobou nedochází k znečišťování ovzduší. </com:P>
  <com:P com:pNumber="85">- Bateriové úložiště umožňuje ukládání přebytků energie pro pozdější použití. </com:P>
  <com:P com:pNumber="86">- Řešení umožnuje napájení při výpadku distribuční sítě. </com:P>
  <com:P com:pNumber="87">- Zvyšuje se energetická nezávislost domu. </com:P>
  <com:P com:pNumber="88">- Výroba energie v místě výroby, což minimalizuje ztráty přenosem. </com:P>
  <com:P com:pNumber="89">- Stabilizace distribuční sítě vlivem rovnoměrnějšího zatížení distribuční sítě. </com:P>
  <com:P com:pNumber="90">- Decentralizace výroby – snižuje závislost na dálkovém přenosu z velkých elektráren. </com:P>
  <com:P com:pNumber="91"> </com:P>
  <com:P com:pNumber="92"> </com:P>
  <com:P com:pNumber="93">Objasnění výkresů  </com:P>
  <com:P com:pNumber="94"> </com:P>
  <com:P com:pNumber="95">Vynález je blíže objasněn pomocí výkresů, na kterých je znázorněno elektrické zapojení budovy vhodné pro použití soupravy a zjednodušené elektrické blokové schéma zapojení soupravy, včetně její aplikace na budovu. </com:P>
  <com:P com:pNumber="96"> </com:P>
  <com:P com:pNumber="97">Na obr. 1 je znázorněno elektrické zapojení budovy předtím, než byla opatřena soupravou podle tohoto vynálezu. </com:P>
  <com:P com:pNumber="98">Na obr. 2 je znázorněno elektrické zapojení soupravy. </com:P>
  <com:P com:pNumber="99">Na obr. 3 je znázorněno zapojení soupravy pro realizaci pro budovu školy.  </com:P>
  <com:P com:pNumber="100">Na obr. 4 je znázorněno zapojení pro realizaci pro rodinný dům. </com:P>
  <com:P com:pNumber="101"> </com:P>
  <com:P com:pNumber="102">
   <com:Br></com:Br>
  </com:P>
  <com:P com:pNumber="103"> </com:P>
  <com:P com:pNumber="104">Příklady uskutečnění vynálezu </com:P>
  <com:P com:pNumber="105"> </com:P>
  <com:P com:pNumber="106">Pro realizaci soupravy pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1, vhodné pro rodinný dům, je k dispozicí unifikovaná řada elektrických komponent, z nichž se podle požadovaného výkonu a požadované kapacity bateriového úložiště 8 zvolí potřebné množství jednotlivých prvků a sestaví se potřebná sada pro konkrétní realizaci vynálezu. </com:P>
  <com:P com:pNumber="107"> </com:P>
  <com:P com:pNumber="108">Znamená to, že každá realizace vynálezu není individuálně projektována, nýbrž pouze podle rozhodnutí o požadavku na zvolený výkon a kapacitu bateriového úložiště 8 se použije příslušné množství unifikovaných elektrických prvků. </com:P>
  <com:P com:pNumber="109"> </com:P>
  <com:P com:pNumber="110">Vynález je opakovatelně využitelný pro jakýkoliv rodinný dům, resp. s ním srovnatelnou budovu.  </com:P>
  <com:P com:pNumber="111"> </com:P>
  <com:P com:pNumber="112">K dispozicí jsou tyto elektrické komponenty: </com:P>
  <com:P com:pNumber="113"> </com:P>
  <com:P com:pNumber="114">FOTOVOLTAICKÉ PANELY 1: K dispozici je dostatečné množství fotovoltaických panelů 1 typu SPDG N120M10 od výrobce Sunpro o jmenovitém výkonu 480 Wp, provedení full-black, glass-glass, mechanická odolnost fotovoltaických panelů 5400 Pa, degradace nominálního výkonu o maximálně 15 % po 30 letech provozu. Každý fotovoltaický panel 1 má nominální výstupní napětí 42,8 V. Fotovoltaické panely 1 jsou vhodné pro umístění na střeše nebo stěně nemovitosti. Každý fotovoltaický panel 1 má podle požadavku kladeného na Vynález jmenovité napětí menší než 120 V DC. </com:P>
  <com:P com:pNumber="115"> </com:P>
  <com:P com:pNumber="116">MIKROSTŘÍDAČE 2: K dispozici jsou mikrostřídače 2 s počtem vstupů 1, 2, 4 nebo 6, výrobce Hoymiles HMS-1600-4T, každý s vlastním MPPT, maximální vstupní DC napětí 165 V, pracovní MPPT rozsah až 60 V, max. DC výkon 1,6 kW, max. účinnost 96,7 %, vlastní spotřeba v noci do 0,05 W, pracovní teplota –40 až +65 °C, krytí: IP67. Mikrostřídač 2 je vhodný pro venkovní montáž. </com:P>
  <com:P com:pNumber="117"> </com:P>
  <com:P com:pNumber="118">HYBRIDNÍ MĚNIČE 7: K dispozici jsou třífázové asymetrické hybridní měniče 7 model BENEKOV 10K SG04LPS EU s parametry: maximální vstupní výkon DC části 13 000 W, rozsah napětí MPPT až 650 V, maximální výstupní výkon a výkon UPS 10 000 W, výstupní frekvence a napětí 50/60 Hz; 380/400 VAC, stupeň ochrany IP65, jmenovitý proud 15,2 A, maximální AC proud 22,7 A, účinnost MPPT 99,9 %, včetně detekce FV oblouku, účiník 0,8, využívající komunikační protokoly RS485, RS232, CAN. </com:P>
  <com:P com:pNumber="119"> </com:P>
  <com:P com:pNumber="120">K dispozici jsou pro jednofázové rozvody rovněž obdobné varianty jednofázových synchronních hybridních měničů 7 téhož výrobce, </com:P>
  <com:P com:pNumber="121"> </com:P>
  <com:P com:pNumber="122">PODRUŽNÉ ELEKTROMĚY 9: K dispozici jsou třífázové digitální podružné elektroměry 9 pro montáž na DIN lištu, EASTRON SDM120D, MID, napětí 400 V AC, frekvence: 50/60 Hz, jmenovitý proud (Ib): 5 A, max. proud (Imax): 45 A, rozběhový proud: cca 0,25 A (0,4 % Ib), třída přesnosti: 1 / B, MID certifikace, pulzní výstup: 1000 imp/kWh (SO+ / SO–), krytí IP51. </com:P>
  <com:P com:pNumber="123"> </com:P>
  <com:P com:pNumber="124">MODULY BATERIOVÉHO ÚLOŽIŠTĚ 8: K dispozici jsou bateriové moduly BENEKOV BATERIX 5K, nominální kapacita baterie 5 kWh, celková kapacita bateriového clustru 20 kWh, 100 % DOD, CZ 38697 U1 - 3 - jmenovité napětí jednoho modulu 51,2 V, rozsah napětí 44,8 V až 55,2 V, maximální nabíjecí/vybíjecí proud 100 A/100 A, komunikační porty CAN 2,0 /RS485, IP ochrana 20, záruka 6000 cyklů nebo 10 let (při 25 ℃, 0.5 C/0.5 C, 90 % D). </com:P>
  <com:P com:pNumber="125"> </com:P>
  <com:P com:pNumber="126">ŘÍDÍCÍ A MONITOROVACÍ JEDNOTKA 6: </com:P>
  <com:P com:pNumber="127"> </com:P>
  <com:P com:pNumber="128">Řídící a monitorovací jednotka 6 sestává z těchto bloků: </com:P>
  <com:P com:pNumber="129"> </com:P>
  <com:P com:pNumber="130">– datové úložiště tvořené nevolatilní polovodičovou pamětí typu Flash, </com:P>
  <com:P com:pNumber="131">– mikropočítač s procesorem řídící a monitorovací jednotky 6. Mikropočítač je opatřen vstupy, které jsou vhodné pro měření proudů a napětí, a výstupy RS232, RS485 a RJ485 pro řízení měničů a baterií. Na mikropočítač jsou napojeny minimálně dva analogové vstupy s komunikačním protokolem RS232, například pro měření teploty a různých napětí.  </com:P>
  <com:P com:pNumber="132"> </com:P>
  <com:P com:pNumber="133">Procesor je tvořen mikrokontrolerem ATMEL z 8bitové řady AVR, konkrétně z řady XMEGA 16D4, vyznačující se vhodnými technickými vlastnostmi a cenovou dostupností. </com:P>
  <com:P com:pNumber="134">– Operační paměť je tvořená statickou operační pamětí typu SRAM, </com:P>
  <com:P com:pNumber="135">– analogové a/nebo digitální vstupy jsou uzpůsobené pro přijímání dat z měniče ve formě napěťových vstupů 0 až 10 V a/nebo proudových vstupů 4 až 20 mA, </com:P>
  <com:P com:pNumber="136">– analogové a/nebo digitální výstupy, jsou tranzistorové (open-collector) a/nebo reléové výstupy určené pro ovládání připojených zátěží. </com:P>
  <com:P com:pNumber="137"> </com:P>
  <com:P com:pNumber="138">Řídící a monitorovací jednotka 6 je uzpůsobena pro:
   
   <com:I> </com:I>
  </com:P>
  <com:P com:pNumber="139"> </com:P>
  <com:P com:pNumber="140">- příjem a ukládání informací o aktuální výrobě fotovoltaických panelů 1 získaných z jednotlivých mikrostřidačů 2. Znamená to, že je schopna přijímat z jednotlivých mikrostřidačů 2 jednotlivých fotovoltaických panelů 1 informace o aktuální výrobě elektrické energie toho kterého fotovoltaického panelu 1. Přitom řídící a monitorovací jednotka 6 je vybavena datovým úložištěm a je schopna tyto informace do něj v digitální formě ukládat. </com:P>
  <com:P com:pNumber="141"> </com:P>
  <com:P com:pNumber="142">Řídící a monitorovací jednotka 6 je uzpůsobena pro získávání a ukládání dat o provozních stavech hybridního měniče 7. Znamená to, že je schopna přijímat informace o aktuálních provozních parametrech hybridního měniče 7, jako jsou například výkon, napětí, proud, stav nabití bateriového úložiště 8, provozní režim nebo případné chybové stavy a tyto informace dále analyzovat a ukládat do interního datového úložiště v digitální podobě. </com:P>
  <com:P com:pNumber="143"> </com:P>
  <com:P com:pNumber="144">Řídící a monitorovací jednotka 6 je uzpůsobena pro zadávání instrukcí k provozu hybridního měniče 7. To znamená, že je schopna aktivně řídit jeho provoz, například nastavovat provozní režimy, řídit tok energie mezi fotovoltaickými panely 1 a bateriovým úložiště 8 a distribuční sítí 3, měnit parametry nabíjení a vybíjení bateriového úložiště 8 nebo spouštět či zastavovat určité funkce hybridního měniče 7 v závislosti na aktuálních podmínkách a požadavcích systému. </com:P>
  <com:P com:pNumber="145"> </com:P>
  <com:P com:pNumber="146">Řídící a monitorovací jednotka 6 je uzpůsobena pro zadávání instrukcí k nabíjení a vybíjení bateriového úložiště 8. To znamená, že je schopna řídit proces ukládání elektrické energie do bateriového úložiště 8 a jejího následného uvolňování podle aktuální potřeby systému, například na základě spotřeby a výroby z fotovoltaických panelů 1. Řídicí a monitorovací jednotka 6 může určovat, kdy a jakou měrou má být bateriové úložiště 8 nabíjeno nebo vybíjeno, a to s cílem optimalizovat energetické toky a zvýšit efektivitu celého systému. </com:P>
  <com:P com:pNumber="147"> </com:P>
  <com:P com:pNumber="148">Uvedené činnosti realizuje řídící a monitorovací jednotka 6 přes hybridní měnič 7. </com:P>
  <com:P com:pNumber="149"> </com:P>
  <com:P com:pNumber="150">Řídící a monitorovací jednotka 6 je uzpůsobena pro příjem, zpracování a ukládání informací z bateriového úložiště 8, získaných z hybridního měniče 7. Znamená to, že je schopna přijímat údaje o aktuálním stavu bateriového úložiště 8, jako je stav nabití, napětí, proud, kapacita nebo teplota, tyto informace dále zpracovávat, analyzovat jejich vývoj v čase a ukládat je do interního datového úložiště pro další využití, například pro řízení energetických toků nebo diagnostiku systému. Uvedené činnosti realizuje řídící a monitorovací jednotka 6 přes hybridní měnič 7. </com:P>
  <com:P com:pNumber="151"> </com:P>
  <com:P com:pNumber="152">SIGNÁLNÍ VEDENÍ 11: Pro realizaci soupravy je k dispozici signální vedení 11. K dispozici je dvojlinka 2 x 0,75mm2 v potřebné délce. </com:P>
  <com:P com:pNumber="153"> </com:P>
  <com:P com:pNumber="154">Souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1 je realizovatelná na nemovitost znázorněnou na obr. 1. Může to být každá nemovitost, jejíž odběrná místa 4 jsou propojena vnitřním elektrickým rozvodem 10, který je napojený přes distribuční elektroměr 5 na distribuční síť 3. </com:P>
  <com:P com:pNumber="155"> </com:P>
  <com:P com:pNumber="156">První příklad uskutečnění vynálezu: </com:P>
  <com:P com:pNumber="157"> </com:P>
  <com:P com:pNumber="158">V prvním příkladu uskutečnění je vynález znázorněn na obr. 2. Úkolem je realizovat soupravu pro výrobu a akumulaci elektrické energie z fotovoltaických panelů pro budovu školy. </com:P>
  <com:P com:pNumber="159"> </com:P>
  <com:P com:pNumber="160">Je požadován výkon fotovoltaických panelů 1 v hodnotě 5 kWp a kapacita bateriového úložiště 8 v hodnotě 15 kWh. Proto je vzhledem k požadovaným parametrům z řady elektrických komponent vybráno následující množství elektrických prvků: </com:P>
  <com:P com:pNumber="161"> </com:P>
  <com:P com:pNumber="162">- 9 kusů fotovoltaických panelů 1,  </com:P>
  <com:P com:pNumber="163">- 9 kusů mikrostřídačů 2, každý opatřený jedním vstupem, </com:P>
  <com:P com:pNumber="164">- 1 kus 3fázového hybridního měniče 7,  </com:P>
  <com:P com:pNumber="165">- 3 ks bateriových modulů pro bateriové úložiště 8, </com:P>
  <com:P com:pNumber="166">- signální vedení 11, </com:P>
  <com:P com:pNumber="167">- pro silové vedení jsou k dispozicí vodiče CYKY-J 5×4 mm². </com:P>
  <com:P com:pNumber="168"> </com:P>
  <com:P com:pNumber="169">K fotovoltaickým panelům 1 jsou připojeny jednotlivé mikrostřídač 2 tak, že na každý panel je připojen jeden mikrostřídač 2.  </com:P>
  <com:P com:pNumber="170"> </com:P>
  <com:P com:pNumber="171">Každý fotovoltaický panel 1 má jmenovité napětí menší než 120 V DC. Každý mikrostřídač 2 má jeden vstup, na který je připojen jeden fotovoltaický panel 1. </com:P>
  <com:P com:pNumber="172"> </com:P>
  <com:P com:pNumber="173">Propojení mikrostřídačů 2 je realizováno na jejich výstupních částech tak, že výstupy všech mikrostřídačů 2 jsou vzájemně propojeny AC kabeláží.  </com:P>
  <com:P com:pNumber="174"> </com:P>
  <com:P com:pNumber="175">Silovým vedením za použití vodičů CYKY-J 5×4 mm² jsou mikrostřídače 2 napojitelné na vnitřní elektrický rozvod 10.  </com:P>
  <com:P com:pNumber="176"> </com:P>
  <com:P com:pNumber="177">Na výstup hybridního měniče 7 jsou napojeny 3 ks bateriových modulů bateriového úložiště 8. </com:P>
  <com:P com:pNumber="178"> </com:P>
  <com:P com:pNumber="179">Na hybridní měnič 7 jsou jedním koncem napojeny 2 metry dvojlinky, tvořící signální vedení 11. </com:P>
  <com:P com:pNumber="180"> </com:P>
  <com:P com:pNumber="181">Druhý konec signálního vedení 11 je určen pro napojení na distribuční elektroměr 5.  </com:P>
  <com:P com:pNumber="182"> </com:P>
  <com:P com:pNumber="183">Takto je vytvořena souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1, která je určena pro použití v budově školy. </com:P>
  <com:P com:pNumber="184"> </com:P>
  <com:P com:pNumber="185">Následně je sestava odzkoušená a je přistoupeno k její aplikaci na budovu školy. Situace je znázorněna na obr. 3 a 4. </com:P>
  <com:P com:pNumber="186"> </com:P>
  <com:P com:pNumber="187">Čtyřpodlažní budova školy má čtyři odběrná místa 4, kterými jsou jednotlivá patra školní budovy. Všechna odběrná místa 4 jsou propojena vnitřním elektrickým rozvodem 10 budovy na distribuční elektroměr 5. Distribuční elektroměr 5 je napojen na distribuční síť 3. </com:P>
  <com:P com:pNumber="188"> </com:P>
  <com:P com:pNumber="189">Fotovoltaické panely 1 včetně mikrospínačů 2 jsou instalovány na střechu školy.  </com:P>
  <com:P com:pNumber="190"> </com:P>
  <com:P com:pNumber="191">Z fotovoltaických panelů 1 přes mikrospínače 2 je silovým vedením CYKY-J 5×4 mm² realizováno propojení na vnitřní elektrický rozvod 10 budovy školy. Napojení výstupů všech mikrostřídačů 2 na vnitřní elektrický rozvod 10 budovy je provedeno v nejvyšším patře budovy školy tak, aby silové vedení nebylo zbytečně dlouhé. </com:P>
  <com:P com:pNumber="192"> </com:P>
  <com:P com:pNumber="193">Na vnitřní elektrický rozvod 10 budovy jsou napojena, resp. již při stavbě školy byly napojeny jednotlivá odběrná místa 4.  </com:P>
  <com:P com:pNumber="194"> </com:P>
  <com:P com:pNumber="195">Na vnitřní elektrický rozvod 10 budovy je ve sklepních prostorách napojen hybridní měnič 7, na který je napojeno bateriové úložiště 8. Bateriové úložiště 8 má jmenovité napětí 51,2 V DC. Bateriové úložiště 8 je tvořeno třemi moduly o kapacitě 5 kWh, celková kapacita 15 kWh. </com:P>
  <com:P com:pNumber="196"> </com:P>
  <com:P com:pNumber="197">Hybridní měnič 7 je na vnitřní elektrický rozvod 10 napojen silovým vedením. </com:P>
  <com:P com:pNumber="198"> </com:P>
  <com:P com:pNumber="199">Hybridní měnič 7 je druhým koncem signálního vedení 11 napojen na distribuční elektroměr 5.  </com:P>
  <com:P com:pNumber="200"> </com:P>
  <com:P com:pNumber="201">Tím je hybridní měnič 7 signálním vedením 11 napojen přímo do distribuční elektroměr 5, což umožňuje snímat hodnoty a směry proudu procházejícím distribučním elektroměrem 5. </com:P>
  <com:P com:pNumber="202"> </com:P>
  <com:P com:pNumber="203">Tím je realizováno napojení soupravy pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1 podle prvního příkladu uskutečnění vynálezu na budovu školy. </com:P>
  <com:P com:pNumber="204"> </com:P>
  <com:P com:pNumber="205">Druhý příklad uskutečnění vynálezu: </com:P>
  <com:P com:pNumber="206"> </com:P>
  <com:P com:pNumber="207">Ve druhém příkladu uskutečnění je vynález realizován pro použití v rodinném domě. </com:P>
  <com:P com:pNumber="208"> </com:P>
  <com:P com:pNumber="209">Rodinný dům je o dvou bytech, které tvoří dvě odběrná místa 4. Každý z bytů je vybaven běžnými bytovými elektrospotřebiči. Třetím odběrným místem 4 je sklepní prostor, zahrnující technickou místnost a garáž, kde je tepelné čerpadlo, nabíjení elektromobilu a sušička prádla. </com:P>
  <com:P com:pNumber="210"> </com:P>
  <com:P com:pNumber="211">Všechna tři odběrná místa 4 jsou propojena vnitřním elektrickým rozvodem 10, kterým jsou napojena na distribuční elektroměr 5 a přes něj na distribuční síť 3. </com:P>
  <com:P com:pNumber="212"> </com:P>
  <com:P com:pNumber="213">Protože spotřeba elektrické energie rodinného domu je vysoká a zatěžuje jeho uživatele vysokými náklady, bylo rozhodnuto realizovat soupravu pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1 podle tohoto vynálezu a napojit ji na rodinný dům. Souprava je znázorněna na obr. 5. </com:P>
  <com:P com:pNumber="214"> </com:P>
  <com:P com:pNumber="215">U druhého příkladu uskutečnění vynálezu soupravy je požadován výkon fotovoltaických panelů 1 ve výši 5 až 6 kWp. Kapacita bateriového úložiště 8 má být 10 kWh. </com:P>
  <com:P com:pNumber="216"> </com:P>
  <com:P com:pNumber="217">Proto je vzhledem k požadovaným parametrům z řady elektrických komponent vybráno následující množství elektrických prvků: </com:P>
  <com:P com:pNumber="218"> </com:P>
  <com:P com:pNumber="219">- 11 kusů fotovoltaických panelů 1, z nichž každý má jmenovité napětí menší než 120 V DC, </com:P>
  <com:P com:pNumber="220">- 6 kusů mikrostřídačů 2, </com:P>
  <com:P com:pNumber="221">- 1 kus 1fázového, asymetrického hybridního měniče 7, </com:P>
  <com:P com:pNumber="222">- 2 kusy bateriových modulů bateriového úložiště 8, </com:P>
  <com:P com:pNumber="223">- 1 kus podružného elektroměru 9, </com:P>
  <com:P com:pNumber="224">- 1 kus řídící a monitorovací jednotky 6, </com:P>
  <com:P com:pNumber="225">- signální vedení 11. </com:P>
  <com:P com:pNumber="226"> </com:P>
  <com:P com:pNumber="227">Pro silové vedení jsou použity vodiče CYKY-J 3×2,5 mm² v dostatečném množství. </com:P>
  <com:P com:pNumber="228"> </com:P>
  <com:P com:pNumber="229">Čtyři mikrostřídače 2 jsou opatřeny každý jedním vstupem, což umožňuje připojení vždy jednoho fotovoltaického panelu 1 ke každému mikrostřídači 2. </com:P>
  <com:P com:pNumber="230"> </com:P>
  <com:P com:pNumber="231">Jeden mikrostřídač 2 má šest vstupů, což umožňuje připojení až šesti fotovoltaických panelů 1. Ke každému ze čtyř vstupů je připojen jeden fotovoltaický panel 1. Dva vstupy mikrostřídače 2 nejsou obsazeny. </com:P>
  <com:P com:pNumber="232"> </com:P>
  <com:P com:pNumber="233">Jeden mikrostřídač 2 má šest vstupů, což umožňuje připojení až šesti fotovoltaických panelů1. Ke každému ze tří vstupů je připojen jeden fotovoltaický panel 1. Tři vstupy mikrostřídače 2 nejsou obsazeny. </com:P>
  <com:P com:pNumber="234"> </com:P>
  <com:P com:pNumber="235">Znamená to, že každý mikrostřídač 2 má jeden až šest vstupů, přičemž k tomuto mikrostřídači 2 je připojen jeden až šest fotovoltaických panelů 1, přičemž na každý vstup každého mikrostřídače 2 je připojen nejvýše jeden fotovoltaický panel 1. </com:P>
  <com:P com:pNumber="236"> </com:P>
  <com:P com:pNumber="237">Následně je přistoupeno k realizaci soupravy přímo na rodinném domě. </com:P>
  <com:P com:pNumber="238"> </com:P>
  <com:P com:pNumber="239">Souprava není sestavována zvlášť, což by bylo výhodné pro její odzkoušení, nýbrž je realizována přímo na rodinném domě. </com:P>
  <com:P com:pNumber="240"> </com:P>
  <com:P com:pNumber="241">Na střechu rodinného domu jsou instalovány fotovoltaické panely 1 a opatřeny mikrospínači 2. Výstupy mikrospínačů 2 jsou napojeny v půdních prostorách na elektrický rozvod 10 rodinného domu. Situaci znázorňuje obr. 6. </com:P>
  <com:P com:pNumber="242"> </com:P>
  <com:P com:pNumber="243">Ve sklepním prostoru rodinného domu je umístěno bateriové úložiště 8, které je propojeno s hybridním měničem 7. Hybridní měnič 7 je silově za použití vodičů CYKY-J 3×2,5 mm² připojen na elektrický rozvod 10 ve sklepním prostoru rodinného domu. </com:P>
  <com:P com:pNumber="244"> </com:P>
  <com:P com:pNumber="245">Protože nebylo vlastníkem distribučního elektroměru 5 umožněno napojit signálním vedením 11 hybridní měnič 7 na vnitřní obvody distribučního elektroměru 5, je v sérii s distribučním elektroměrem 5 napojen podružný elektroměr 9.  </com:P>
  <com:P com:pNumber="246"> </com:P>
  <com:P com:pNumber="247">Hybridní měnič 7 je signálním vedením 11 napojen na podružný elektroměr 9, čímž je umožněno snímání hodnot a směru proudů procházejících podružným elektroměrem 9. Distribuční elektroměr 5 a podružný elektroměr 9 jsou napojeny v sérii. Proto informace o proudech v podružném elektroměru 9 a v distribučním elektroměru 5 jsou shodné. </com:P>
  <com:P com:pNumber="248"> </com:P>
  <com:P com:pNumber="249">Na hybridní měnič 7 je rovněž napojena řídící a monitorovací jednotka 6.  </com:P>
  <com:P com:pNumber="250"> </com:P>
  <com:P com:pNumber="251">Řídící a monitorovací jednotka 6 je připojena na každý mikrostřídač 2. Připojení je realizováno signálním vedením 11. Přitom je možno využít dálkový, bezdrátový přenos informací, čímž by se odstranila nutnost realizace signálního vedení 11 ze střechy rodinného domu do sklepních prostor, kde je umístěna monitorovací jednotka 6. </com:P>
  <com:P com:pNumber="252"> </com:P>
  <com:P com:pNumber="253">Funkce soupravy pro výrobu a akumulaci elektrické energie z fotovoltaických panelů 1 podle tohoto vynálezu je v obou příkladech uskutečnění obdobná. </com:P>
  <com:P com:pNumber="254"> </com:P>
  <com:P com:pNumber="255">Fotovoltaické panely 1 vyrábějí elektrickou energii přeměnou slunečního záření, resp. přeměnou energie světla. Tento proces probíhá v jednotlivých fotovoltaických článcích fotovoltaických panelů 1. </com:P>
  <com:P com:pNumber="256"> </com:P>
  <com:P com:pNumber="257">Energie z jednotlivých fotovoltaických panelů 1, resp. stejnosměrný proud z fotovoltaických panelů 1, je v mikrostřídačích 2 přeměněn na střídavý elektrický proud o napětí 230 V AC a současně upraven na střídavé napětí kompatibilní s napětím distribuční sítě 3, tj. na napětí se shodnou frekvencí, velikostí a fází, jaké má distribuční síť 3. </com:P>
  <com:P com:pNumber="258"> </com:P>
  <com:P com:pNumber="259">Výroba z fotovoltaických panelů 1 není nijak omezována. Fotovoltaickými panely 1 vyráběná elektrická energie je předávána vnitřním elektrickým rozvodem 10 pro potřebu všech odběrných míst 4. </com:P>
  <com:P com:pNumber="260"> </com:P>
  <com:P com:pNumber="261">Hybridní měnič 7 má k dispozicí informace o velikosti proudu a směru proudu, který prochází distribučním elektroměrem 5, a to přímo z distribučního elektroměru 5 (v prvním příkladu uskutečnění) nebo z podružného elektroměru 9 (v druhém příkladu uskutečnění). </com:P>
  <com:P com:pNumber="262"> </com:P>
  <com:P com:pNumber="263">Pokud hybridní měnič 7 zjistí, že výroba elektrické energie z fotovoltaických panelů 1 je vyšší, než je souhrnná spotřeba odběrných míst 4, nabíjí tímto přetokem bateriové úložiště 8.
   
   <com:I> </com:I>
   <com:I> </com:I>
  </com:P>
  <com:P com:pNumber="264"> </com:P>
  <com:P com:pNumber="265">Pokud je výroba elektrické energie z fotovoltaických panelů 1 nedostatečná, vybíjí hybridní měnič 7 bateriové úložiště 8 ve prospěch odběrných míst 4.  </com:P>
  <com:P com:pNumber="266"> </com:P>
  <com:P com:pNumber="267">Přitom je stále k dispozicí elektrická energie z distribuční sítě 3, která kryje případný deficit vzniklý nedostatkem výroby elektrické energie z fotovoltaických panelů 1 za současného vybitého bateriového úložiště 8.
   
   <com:I> </com:I>
   <com:I> </com:I>
  </com:P>
  <com:P com:pNumber="268"> </com:P>
  <com:P com:pNumber="269">Řídící a monitorovací jednotka 6 získává informace o stavu nabití bateriového úložiště 8 z hybridního měniče 7. Stejně tak získává informace o velikosti a směru proudů procházejícím distribučním elektroměrem 5. </com:P>
  <com:P com:pNumber="270"> </com:P>
  <com:P com:pNumber="271">Řídící a monitorovací jednotka 6 rovněž napojením na mikrostřídače 2 získává informace z fotovoltaických panelů 1. </com:P>
  <com:P com:pNumber="272"> </com:P>
  <com:P com:pNumber="273">Může tak ukládat na jedno společné místo data o výrobě z fotovoltaických panelů 1, z bateriového úložiště 8 i data z hybridního měniče 7. Tato data se mohou následně zobrazit v jedné společné aplikaci. </com:P>
  <com:P com:pNumber="274"> </com:P>
  <com:P com:pNumber="275">Hybridní měnič 7 není vůbec napojen na fotovoltaické panely 1 a nijak s nimi nekomunikuje. Hybridní měnič 7 získává data o výrobě z fotovoltaických panelů 1 nepřímo z podružného elektroměru 9 nebo z distribučního elektroměru 5, resp. má informace, zda je výroba z fotovoltaických panelů 1 dostatečná či nikoliv. </com:P>
  <com:P com:pNumber="276"> </com:P>
  <com:P com:pNumber="277">Jedná se v zásadě o dva samostatné systémy. Fotovoltaické panely 1 a mikrostřídače 2 zajišťují výrobu elektrické energie. Hybridní měnič 7 zajišťuje nabíjení a vybíjení bateriového úložiště 8.  </com:P>
  <com:P com:pNumber="278"> </com:P>
  <com:P com:pNumber="279">Předložený systém řízení je vhodný pro menší budovy, zejména rodinné domy, které mohou mít více odběrných míst 4, ale hradí elektrickou energii společně za všechna odběrná místa 4. </com:P>
  <com:P com:pNumber="280"> </com:P>
  <com:P com:pNumber="281">Zařízení podle tohoto vynálezu není nutno individuálně vyrábět nebo technicky přizpůsobovat pro každý jednotlivý případ použití zvlášť. Zařízení je plně unifikované. Sestává z přesně definovaných, shodných elektrických prvků. Každá realizace se liší pouze počtem jednotlivých komponent, zejména počtem fotovoltaických panelů 1 a odpovídajícího množství mikrostřídačů 2 a počtem modulů pro bateriové úložiště 8. </com:P>
  <com:P com:pNumber="282"> </com:P>
  <com:P com:pNumber="283">Množství fotovoltaických panelů 1 je předurčeno zvoleným výkonem zařízení. </com:P>
  <com:P com:pNumber="284"> </com:P>
  <com:P com:pNumber="285">Požadovaná kapacita bateriového úložiště 8 se dosahuje paralelním spojením zvoleného počtu bateriových modulů. </com:P>
  <com:P com:pNumber="286"> </com:P>
  <com:P com:pNumber="287">Unifikace sestavy umožňuje majiteli budovy stanovit si požadavek na výkon fotovoltaických panelů 1 a kapacitu bateriového úložiště 8 a dle toho pouze zvolit počet jednotlivých typizovaných elektrických prvků, ze kterých zařízení bude sestávat. </com:P>
  <com:P com:pNumber="288"> </com:P>
  <com:P com:pNumber="289"> </com:P>
  <com:P com:pNumber="290">Průmyslová využitelnost  </com:P>
  <com:P com:pNumber="291"> </com:P>
  <com:P com:pNumber="292">Předložený vynález je určen k výrobě elektrické energie primárně pro rodinný dům. </com:P>
  <com:P com:pNumber="293"> </com:P>
  <com:P com:pNumber="294">Předložený vynález je opakovatelný a průmyslově využitelný, protože je konstruován tak, aby jej bylo možné sériově vyrábět, standardizovat v rámci typizovaných provedení a jako hotový výrobek dodávat na trh širokému okruhu odběratelů.  </com:P>
  <com:P com:pNumber="295"> </com:P>
  <com:P com:pNumber="296">Při provozu slouží vynález k výrobě elektrické energie, která je přednostně využívána pro spotřebu všech odběrných míst v budově a následně při přetoku k nabíjení bateriového úložiště bytového domu. </com:P>
  <com:P com:pNumber="297"> </com:P>
  <com:P com:pNumber="298">Vynález splňuje podmínku průmyslové využitelnosti, neboť je objektivně a opakovaně proveditelný v rámci průmyslové výroby, montáže a provozu a je využitelný v hospodářské činnosti subjektů působících v oblasti výstavby, správy a provozu objektů v energetice. </com:P>
  <com:P com:pNumber="299"> </com:P>
  <com:P com:pNumber="300">Vynález má kladný vliv na bezpečnost provozu, protože se na něm vyskytuje stejnosměrné napětí v maximální hodnotě 120 V DC, přičemž střídavé napětí je obvyklých napěťových parametrů. </com:P>
  <com:P com:pNumber="301"> </com:P>
  <com:P com:pNumber="302">Souprava a její aplikace na každý rodinný dům, resp. budovu obdobného rozsahu, je plně opakovatelná, když je realizovatelná v standardním provedení. </com:P>
  <pat:DrawingDescription>
   <com:P>      1 - fotovoltaický panel
    
    <com:Br></com:Br>      2 - mikrostřídač
    
    <com:Br></com:Br>      3 - distribuční síť
    
    <com:Br></com:Br>      4 - odběrné místo
    
    <com:Br></com:Br>      5 - distribuční elektroměr
    
    <com:Br></com:Br>      6 - řídící a monitorovací jednotka
    
    <com:Br></com:Br>      7 - hybridní měnič
    
    <com:Br></com:Br>      8 - bateriové úložiště
    
    <com:Br></com:Br>      9 - podružný elektroměr
    
    <com:Br></com:Br>    10 - vnitřní elektrický rozvod
    
    <com:Br></com:Br>    11 - signální vedení
   
   </com:P>
  </pat:DrawingDescription>
 </pat:Description>
 <pat:Claims xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0">
  <pat:Claim>
   <pat:ClaimNumber>1</pat:ClaimNumber>
   <pat:ClaimText>Souprava pro výrobu a akumulaci elektrické energie z fotovoltaických panelů (1), vhodná pro budovu, zejména rodinný dům, jehož odběrná místa (4) jsou propojena vnitřním elektrickým rozvodem (10), který je napojený přes distribuční elektroměr (5) na distribuční síť (3),
    
    <com:Br></com:Br>
    <com:B>vyznačující se tím, </com:B>že
    
    <com:B> </com:B>zahrnuje:
    
    <com:Br></com:Br>- fotovoltaické panely (1), z nichž každý má jmenovité napětí menší než 120 V DC,
    
    <com:Br></com:Br>- mikrostřídače (2),
    
    <com:Br></com:Br>- hybridní měnič (7),
    
    <com:Br></com:Br>- bateriové úložiště (8)
    
    <com:I> </com:I>s maximálním napětím menším než 120 V DC,
    
    <com:Br></com:Br>- signální vedení (11),
    
    <com:Br></com:Br>přičemž každý mikrostřídač (2) má jeden až šest vstupů, přičemž k tomuto mikrostřídači (2) je připojen jeden až šest fotovoltaických panelů (1), přičemž na každý vstup každého mikrostřídače (1) je připojen nejvýše jeden fotovoltaický panel (1),
    
    <com:Br></com:Br>přičemž na vnitřní elektrický rozvod (10) budovy jsou napojitelné:
    
    <com:Br></com:Br>- výstupy všech mikrostřídačů (2),
    
    <com:Br></com:Br>- a hybridní měnič (7) s bateriovým úložištěm (8),
    
    <com:Br></com:Br>přičemž hybridní měnič (7) je signálním vedením (11) napojitelný na distribuční elektroměr (5)
    
    <com:Br></com:Br>nebo
    
    <com:Br></com:Br>souprava dále zahrnuje podružný elektroměr (9), jehož výstup je napojen na vnitřní elektrický rozvod (10) budovy a jehož vstup je napojitelný na výstup distribučního elektroměru (5), přičemž v tomto uspořádání je hybridní měnič (7) signálním vedením (11) připojen na podružný elektroměr (9).
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>2</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle nároku 1, 
    
    <com:B>vyznačující se tím</com:B>, že zahrnuje řídící a monitorovací jednotku (6), která je signálním vedením (11) propojena s hybridním měničem (7) a každým mikrostřídačem (2),
    
    <com:Br></com:Br>přičemž
    
    <com:I> </com:I>řídící a monitorovací jednotka (6) zahrnuje:
    
    <com:Br></com:Br>- datové úložiště,
    
    <com:I> </com:I>
    <com:Br></com:Br>- mikropočítač s procesorem,
    
    <com:Br></com:Br>- operační paměť,
    
    <com:Br></com:Br>- analogové a/nebo digitální vstupy,
    
    <com:Br></com:Br>- analogové a/nebo digitální výstupy,
    
    <com:Br></com:Br>a je uzpůsobena pro:
    
    <com:Br></com:Br>- příjem a ukládání informací o aktuální výrobě fotovoltaických panelů (1), získaných z jednotlivých mikrostřidačů (2),
    
    <com:Br></com:Br>- získávání a ukládání dat o provozních stavech hybridního měniče (7),
    
    <com:Br></com:Br>- zadávání instrukcí k provozu hybridního měniče (7),
    
    <com:Br></com:Br>- zadávání instrukcí k nabíjení a vybíjení bateriového úložiště (8) přes hybridní měnič (7),
    
    <com:Br></com:Br>- příjem, zpracování a ukládání informací z bateriového úložiště (8), získaných z hybridního měniče (7).
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>3</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle nároku 1 nebo 2, 
    
    <com:B>vyznačující se tím</com:B>,
    
    <com:B> </com:B>že
    
    <com:B> </com:B>výstupů všech mikrostřídačů (2) jsou určeny k napojení na vnitřní elektrický rozvod (10) budovy, a to v nejvyšším podlaží nebo v půdních prostorách.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>4</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle nároku 1 nebo 2, 
    
    <com:B>vyznačující se tím, </com:B>že hybridní měnič (7) je asymetrický.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>5</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle některého z nároků 1, 2, 4, 
    
    <com:B>vyznačující se tím, </com:B>že hybridní měnič (7) je 3fázový.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>6</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle některého z nároků 1, 2, 4, 5, 
    
    <com:B>vyznačující se tím</com:B>,
    
    <com:B> </com:B>že bateriové úložiště (8) je tvořeno články technologie LFP nebo LTO.
   
   </pat:ClaimText>
  </pat:Claim>
  <pat:Claim>
   <pat:ClaimNumber>7</pat:ClaimNumber>
   <pat:ClaimText>Souprava podle některého z předchozích nároků, 
    
    <com:B>vyznačující se tím, </com:B>že maximální DC napětí mezi jakýmikoliv dvěma DC body soupravy nedosáhne 120 V DC.
   
   </pat:ClaimText>
  </pat:Claim>
 </pat:Claims>
 <pat:Abstract xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0" com:id="abs-1" com:languageCode="cs">
  <com:P com:pNumber="1">Souprava zahrnuje fotovoltaické panely (1), z nichž každý má jmenovité napětí menší než 120 V DC, mikrostřídače (2), hybridní měnič (7), bateriové úložiště (8)
   
   <com:I> </com:I>s maximálním napětím menším než 120 V. K mikrostřídačům (2) jsou připojeny fotovoltaické panely (1). Na vnitřní elektrický rozvod (10) budovy jsou napojitelné výstupy mikrostřídačů (2) a hybridní měnič (7) s bateriovým úložištěm (8). Přes distribuční elektroměr (5) je napojena distribuční síť (3). Hybridní měnič (7) je signálním vedením (11) napojitelný na distribuční elektroměr (5) nebo na podružný elektroměr (9). Součástí soupravy může být řídící a monitorovací jednotku (6), která je signálním vedením (11) propojena s hybridním měničem (7) a každým mikrostřídačem (2). Maximální DC napětí mezi jakýmikoliv dvěma DC body soupravy nedosáhne 120 V DC.
  
  </com:P>
 </pat:Abstract>
 <pat:Drawings xmlns:tbl="http://www.oasis-open.org/tables/exchange/1.0">
  <pat:Figure>
   <pat:FigureNumber>1</pat:FigureNumber>
   <com:Image com:id="img-1" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0001.jpg</com:FileName>
    <com:Alt>Obr. 1</com:Alt>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>2</pat:FigureNumber>
   <com:Image com:id="img-2" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0002.jpg</com:FileName>
    <com:Alt>Obr. 2</com:Alt>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>3</pat:FigureNumber>
   <com:Image com:id="img-3" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0003.jpg</com:FileName>
    <com:Alt>Obr. 3</com:Alt>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>4</pat:FigureNumber>
   <com:Image com:id="img-4" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0004.jpg</com:FileName>
    <com:Alt>Obr. 4</com:Alt>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>5</pat:FigureNumber>
   <com:Image com:id="img-5" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0005.jpg</com:FileName>
    <com:Alt>Obr. 5</com:Alt>
   </com:Image>
  </pat:Figure>
  <pat:Figure>
   <pat:FigureNumber>6</pat:FigureNumber>
   <com:Image com:id="img-6" com:imageContentCategory="Drawing" com:orientationCategory="Landscape">
    <com:ImageFormatCategory>JPEG</com:ImageFormatCategory>
    <com:FileName>2668936img0006.jpg</com:FileName>
    <com:Alt>Obr. 6</com:Alt>
   </com:Image>
  </pat:Figure>
 </pat:Drawings>
</pat:PatentPublication>