<?xml version="1.0" encoding="UTF-8"?>
<!DOCTYPE ep-patent-document SYSTEM "OpenDataPatent_cz.dtd">
<ep-patent-document lang="en" file="OpendataIPOCZ_PT_DIFF_PUV2024-42070.xml" country="CZ" doc-number="38486" kind="U1">
  <bibliographic-data country="CZ">
    <publication-reference>
      <document-id>
        <country>CZ</country>
        <doc-number>38486</doc-number>
        <kind>U1</kind>
        <date>2025-04-15</date>
      </document-id>
    </publication-reference>
    <classifications-ipcr>
      <classification-ipcr sequence="1">
        <section>H</section>
        <class>02</class>
        <subclass>J</subclass>
        <main-group>3</main-group>
        <subgroup>18</subgroup>
        <ipc-version-indicator>
          <date>20060101</date>
        </ipc-version-indicator>
        <classification-level>A</classification-level>
        <symbol-position>F</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
        <generating-office>
          <country>CZ</country>
        </generating-office>
      </classification-ipcr>
      <classification-ipcr sequence="2">
        <section>H</section>
        <class>01</class>
        <subclass>M</subclass>
        <main-group>10</main-group>
        <subgroup>44</subgroup>
        <ipc-version-indicator>
          <date>20060101</date>
        </ipc-version-indicator>
        <classification-level>A</classification-level>
        <symbol-position>L</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
        <generating-office>
          <country>CZ</country>
        </generating-office>
      </classification-ipcr>
      <classification-ipcr sequence="3">
        <section>H</section>
        <class>01</class>
        <subclass>M</subclass>
        <main-group>10</main-group>
        <subgroup>46</subgroup>
        <ipc-version-indicator>
          <date>20060101</date>
        </ipc-version-indicator>
        <classification-level>A</classification-level>
        <symbol-position>L</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
        <generating-office>
          <country>CZ</country>
        </generating-office>
      </classification-ipcr>
    </classifications-ipcr>
    <classifications-cpc>
      <classification-cpc sequence="1">
        <cpc-version-indicator>
          <date>20230801</date>
        </cpc-version-indicator>
        <section>H</section>
        <class>02</class>
        <subclass>J</subclass>
        <main-group>3</main-group>
        <subgroup>18</subgroup>
        <symbol-position>F</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <generating-office>
          <country>CZ</country>
        </generating-office>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
      </classification-cpc>
      <classification-cpc sequence="2">
        <cpc-version-indicator>
          <date>20130101</date>
        </cpc-version-indicator>
        <section>H</section>
        <class>01</class>
        <subclass>M</subclass>
        <main-group>10</main-group>
        <subgroup>44</subgroup>
        <symbol-position>L</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <generating-office>
          <country>CZ</country>
        </generating-office>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
      </classification-cpc>
      <classification-cpc sequence="3">
        <cpc-version-indicator>
          <date>20130101</date>
        </cpc-version-indicator>
        <section>H</section>
        <class>01</class>
        <subclass>M</subclass>
        <main-group>10</main-group>
        <subgroup>46</subgroup>
        <symbol-position>L</symbol-position>
        <classification-value>I</classification-value>
        <action-date>
          <date>20250331</date>
        </action-date>
        <generating-office>
          <country>CZ</country>
        </generating-office>
        <classification-status>B</classification-status>
        <classification-data-source>H</classification-data-source>
      </classification-cpc>
    </classifications-cpc>
    <application-reference>
      <document-id>
        <country>CZ</country>
        <doc-number>2024-42070</doc-number>
        <date>2024-06-27</date>
      </document-id>
    </application-reference>
    <language-of-filing>cs</language-of-filing>
    <language-of-publication>cs</language-of-publication>
    <priority-claims>
      <priority-claim sequence="1" kind="national">
        <country>CZ</country>
        <date>2024-06-27</date>
      </priority-claim>
    </priority-claims>
    <invention-title lang="CS">Souprava pro využití přebytků elektrické energie z obnovitelného zdroje, vhodná zejména pro bytový dům</invention-title>
    <invention-title lang="EN">An assembly to utilise the excess electricity from a renewable source, particularly suitable for an apartment house</invention-title>
  </bibliographic-data>
  <description id="desc" lang="cs">
    <p num="1">
      <b>Souprava pro využití přebytků elektrické energie z obnovitelného zdroje, vhodná zejména pro bytový dům</b>
    </p>
    <p num="2"> </p>
    <p num="3"> </p>
    <p num="4">Oblast techniky </p>
    <p num="5"> </p>
    <p num="6">Technické řešení se týká soupravy pro racionální využití přebytků elektrické energie získané z obnovitelného zdroje elektrické energie. Souprava je vhodná zejména pro bytový dům, u kterého jsou obnovitelným zdrojem fotovoltaické panely. </p>
    <p num="7"> </p>
    <p num="8">Dosavadní stav techniky </p>
    <p num="9"> </p>
    <p num="10">V současné době není známé žádné zařízení, které by jednoduchou cestou řešilo zvýšení odběru elektrické energie z obnovitelného zdroje při jeho momentálním přebytku. </p>
    <p num="11">Zejména při použití obnovitelných zdrojů, kterými jsou fotovoltaické panely, nastávají značné potíže při mimořádně slunečném počasí, kdy výroba elektrické energie z fotovoltaických panelů je značná a její spotřeba právě v době slunečného počasí nebývá vysoká. Může proto docházet k poruchám energetického systému, který není schopen dostatečně rychle reagovat na momentální nadvýrobu elektrické energie z fotovoltaických panelů. </p>
    <p num="12"> </p>
    <p num="13">Podstata technického řešení </p>
    <p num="14"> </p>
    <p num="15">Uvedené nevýhody do jisté míry odstraňuje souprava pro využití přebytků elektrické energie z obnovitelného zdroje podle tohoto technického řešení, která je vhodná zejména pro bytový dům opatřený obnovitelným zdrojem elektrické energie, kterým jsou fotovoltaické panely. Souprava je použitelná pro případ, že obnovitelný zdroj elektrické energie je napojený přes<b> </b>měnič na elektroměr některého odběrného místa elektrické energie. </p>
    <p num="16">Podstata technického řešení spočívá v tom, že souprava sestává z měřiče výkonu obnovitelného zdroje, alespoň jednoho spínače spojeného s alespoň jedním místem odběru přebytků elektrické energie a řídící jednotky. </p>
    <p num="17">Přitom řídící jednotka je svým hardwarem a naprogramovaným softwarem uzpůsobená zejména pro následující úkony:  </p>
    <p num="18">-  snímání údajů z měřiče výkonu, </p>
    <p num="19">-  snímání údajů z elektroměru,  </p>
    <p num="20">-  získávání údajů z měniče,  </p>
    <p num="21">-  vyhodnocování získaných údajů a rozhodování, zda je momentálně vyráběná elektrická energie přebytková,  </p>
    <p num="22">-  ovládání spínačů. </p>
    <p num="23"> </p>
    <p num="24">Měřič výkonu je připojen na obnovitelný zdroj elektrické energie a sdělovacími vodiči propojen s řídící jednotkou. Na řídící jednotku jsou rovněž připojeny měnič, všechny spínače a elektroměr. </p>
    <p num="25"> </p>
    <p num="26">S výhodou souprava dále obsahuje měřič množství elektrické energie, který je umístěný mezi měnič a elektroměr a je propojený s řídící jednotkou nebo je propojený s měničem, který je vždy propojen s řídící jednotkou. </p>
    <p num="27"> </p>
    <p num="28">Výhodné je, pokud je součástí soupravy bateriové úložiště, které je opatřeno indikátorem stavu naplnění bateriového úložiště. Protože obvykle je systém aplikován na bytový dům, je bateriovým úložištěm opatřen tento bytový dům. Indikátor stavu naplnění bateriového úložiště je propojením spojen s řídící jednotkou. </p>
    <p num="29"> </p>
    <p num="30">Výhodou je, pokud je na vstup řídící jednotky napojen informační zdroj predikce počasí. Napojení informačního zdroje predikce počasí na vstup řídící jednotky je realizováno internetovým vstupem, když informační zdroj predikce počasí je známým způsobem dosažitelný přes internetovou síť. V tom případě je řídící jednotka uzpůsobena pro příjem informací z informačního zdroje predikce počasí. </p>
    <p num="31"> </p>
    <p num="32">Rovněž je výhodné, pokud je na vstup řídící jednotky napojen informační zdroj spotové ceny elektrické energie. Napojení informačního zdroje spotové ceny elektrické energie je realizováno internetovým vstupem, když informační zdroj spotové ceny elektrické energie je známým způsobem dosažitelný přes internetovou síť. V tom případě je řídící jednotka uzpůsobena rovněž pro příjem informací z informačního zdroje spotové ceny elektrické energie. </p>
    <p num="33"> </p>
    <p num="34">Pro větší účinnost převodu stejnosměrného napětí obnovitelného zdroje na střídavé napětí distribuční sítě je k měniči, který je uzpůsoben pro komunikaci s bateriovým úložištěm, paralelně připojen střídač propojený propojením s řídící jednotkou.  </p>
    <p num="35"> </p>
    <p num="36">Některá propojení nebo všechna propojení mohou být provedena drátovou nebo bezdrátovou technologií. Pro volbu jedné z těchto možnosti obvykle rozhoduje vzdálenost propojovaných míst. </p>
    <p num="37"> </p>
    <p num="38"> </p>
    <p num="39">Objasnění výkresů </p>
    <p num="40"> </p>
    <p num="41">Technické řešení je blíže objasněno pomocí výkresů, na kterých je znázorněno schéma zapojení soupravy pro využití přebytků elektrické energie z obnovitelného zdroje podle tohoto technického řešení. Souprava pro využití přebytků elektrické energie je znázorněna při použití na bytovém domě. </p>
    <p num="42"> </p>
    <p num="43">Na obr.1 je znázorněn bytový dům se čtyřmi odběrnými místy, který je opatřený obnovitelným zdrojem elektrické energie napojeným přes<b> </b>měnič na elektroměr nejníže umístěného odběrného místa elektrické energie, který je napojen na distribuční síť. Obnovitelným zdrojem elektrické energie jsou fotovoltaické panely. </p>
    <p num="44"> </p>
    <p num="45">Souprava pro využití přebytků elektrické energie z obnovitelného zdroje sestává z měřiče výkonu zdroje, řídící jednotky a spínačů, z nichž každý je spojený s alespoň jedním místem odběru přebytků elektrické energie. Na řídící jednotku jsou napojeny oba spínače, elektroměr, měřiče výkonu a měnič. </p>
    <p num="46"> </p>
    <p num="47">Na obr. 2 je znázorněn bytový dům se čtyřmi odběrnými místy, který je opatřený obnovitelným zdrojem elektrické energie, napojeným přes<b> </b>měnič na elektroměr nejníže umístěného odběrného místa elektrické energie. Elektroměr je napojen na distribuční síť. Obnovitelným zdrojem elektrické energie jsou fotovoltaické panely. </p>
    <p num="48"> </p>
    <p num="49">Souprava pro využití přebytků elektrické energie z obnovitelného zdroje sestává z měřiče výkonu, řídící jednotky a spínačů, z nichž každý je spojený s alespoň jedním místem odběru přebytků elektrické energie. Součástí soupravy je bateriové úložiště. Bateriové úložiště je opatřeno indikátorem stavu naplnění bateriového úložiště. Na řídící jednotku je napojen informační zdroj predikce počasí a rovněž informační zdroj spotové ceny elektrické energie. </p>
    <p num="50"> </p>
    <p num="51">Na obr. 3 je znázorněn bytový dům se čtyřmi odběrnými místy. Bytový dům je opatřen obnovitelným zdrojem elektrické energie, tvořeným fotovoltaickými panely. </p>
    <p num="52"> </p>
    <p num="53">Bytový dům je opatřen řídící jednotkou a bateriovým úložištěm. Rovněž je opatřen měničem, ke kterému je paralelně připojen střídač. </p>
    <p num="54"> </p>
    <p num="55">Souprava pro využití přebytků elektrické energie z obnovitelného zdroje sestává z měřiče výkonu, řídící jednotky a spínačů, z nichž každý je spojený alespoň s jedním místem odběru přebytků elektrické energie. Součástí soupravy je bateriové úložiště. Bateriové úložiště je opatřeno indikátorem stavu naplnění bateriového úložiště. Na řídící jednotku je napojen informační zdroj predikce počasí a rovněž informační zdroj spotové ceny elektrické energie. </p>
    <p num="56"> </p>
    <p num="57">K měniči, který je uzpůsoben pro komunikaci s bateriovým úložištěm, je paralelně připojen střídač propojený propojením s řídící jednotkou. </p>
    <p num="58"> </p>
    <p num="59"> </p>
    <p num="60">Příklady uskutečnění technického řešení </p>
    <p num="61"> </p>
    <p num="62">První příkladné uskutečnění je znázorněno na obr. 1. Bytový dům o čtyřech bytových jednotkách, tvořících čtyři odběrná místa 3, je opatřen obnovitelným zdrojem 1 elektrické energie, kterým jsou fotovoltaické panely o výkonu 10 kWp, umístěné na střeše bytového domu. Obnovitelný zdroj 1 elektrické energie je opatřen měřičem 2 okamžitého výkonu, což je wattmetr.  </p>
    <p num="63"> </p>
    <p num="64">Obnovitelný zdroj 1 elektrické energie je napojen přes měnič 5 na elektroměr 16 odběrného místa 3 elektrické energie, který je v přízemí bytového domu. Tento obousměrný elektroměr 16 je napojen na distribuční síť 14. </p>
    <p num="65"> </p>
    <p num="66">Souprava pro využití přebytků elektrické energie z obnovitelného zdroje 1 sestává z měřiče 2 výkonu, dvou spínačů 7 s místy 8 odběru přebytků elektrické energie a řídící jednotky 6.  </p>
    <p num="67"> </p>
    <p num="68">Spínače 7 s místem 8 odběru přebytků elektrické energie jsou instalovány pouze ve dvou bytech, tj. ve dvou odběrných místech 3. Na jeden spínač 7 je napojeno jedno místo 8 odběru přebytků elektrické energie.  </p>
    <p num="69"> </p>
    <p num="70">Na druhý spínač 7 jsou napojena dvě místa 8 odběru přebytků elektrické energie. </p>
    <p num="71"> </p>
    <p num="72">Místy 8 odběru přebytků elektrické energie jsou běžné zásuvky. </p>
    <p num="73"> </p>
    <p num="74">Elektroměr 16, na který je přivedena elektrická energie z obnovitelného zdroje 1, stejně jako další tři elektroměry 16 dalších odběrných míst 3, je napojen na distribuční síť 14. </p>
    <p num="75"> </p>
    <p num="76">Elektroměr 16, na který je přivedena elektrická energie z obnovitelného zdroje 1, je napojen propojením 12 na řídící jednotku 6. Propojení 12 je realizováno běžnými slaboproudými vodiči. Na řídící jednotku 6 je rovněž propojením 12 napojen měnič 5 a měřič 2 výkonu tohoto obnovitelného zdroje 1. Na řídící jednotku 6 jsou rovněž propojením 12 napojeny všechny spínače 7 míst 8 odběru přebytků elektrické energie, které jsou umístěné v bytových jednotkách bytového domu, tj. v odběrných místech 3 elektrické energie. </p>
    <p num="77"> </p>
    <p num="78">Ve druhém příkladném uskutečnění, znázorněném na obr. 2, je souprava pro využití přebytků elektrické energie z obnovitelného zdroje 1 sestávající z měřiče 2, pěti spínačů 7, každý s jedním místem 8 odběru přebytků elektrické energie. Souprava dále obsahuje měřič 13 množství elektrické energie proudící do elektroměru 16, bateriové úložiště 4, které je o kapacitě 600 Ah a napětí 50 V, a řídící jednotku 6.  </p>
    <p num="79"> </p>
    <p num="80">Spínače 7 s místy 8 odběru přebytků elektrické energie jsou určeny pro instalaci ve třech bytech, tj. ve třech odběrných místech 3. Na každý jeden spínač 7 je napojeno jedno místo 8 odběru přebytků elektrické energie. V jednom odběrném místě 3 má být instalován jeden spínač 7, ve druhém bytě rovněž jeden spínač 7 a ve třetím bytě jsou tři spínače 7. </p>
    <p num="81"> </p>
    <p num="82">Po instalaci soupravy pro využití přebytků elektrické energie z obnovitelného zdroje 1 na bytový dům je situace následující: </p>
    <p num="83"> </p>
    <p num="84">Bytový dům o čtyřech bytových jednotkách, tvořících čtyři odběrná místa 3, je opatřen bateriovým úložištěm 4 o kapacitě 600 Ah a napětí 50 V. Bateriové úložiště 4 je opatřeno indikátorem 9 stavu naplnění bateriového úložiště 4, který pracuje na bázi přesného měření napětí bateriového úložiště 4. Mezi měnič 5 a elektroměr 16 je vložen měřič 13 množství elektrické energie, tvořený elektroměrem 16 známé konstrukce, který je propojením 12 propojen s řídící jednotkou 6. Místa 8 odběru přebytků elektrické energie jsou instalována ve třech bytech, přitom v jednom z nich jsou tři spínače 7, a na každý z nich je napojeno jedno místo 8 odběru přebytků elektrické energie. </p>
    <p num="85"> </p>
    <p num="86">Na obnovitelný zdroj 1 je napojen měřič 2, který je propojením 12 přes měnič 5 propojen na řídící jednotku 6.  </p>
    <p num="87"> </p>
    <p num="88">Na řídící jednotku 6 je propojením 12 rovněž napojen měřič 13 množství elektrické energie, měnič 5 a každý spínač 7. Dále je na řídící jednotku 6 napojený informační zdroj 11 predikce počasí a rovněž informační zdroj 10 spotové ceny elektrické energie. Z informačního zdroje 11 predikce počasí a rovněž z informačního zdroje 10 spotové ceny elektrické energie jsou údaje vkládány do řídící jednotky 6 přes internetovou síť, na kterou je řídící jednotka 6 známým způsobem napojena a přes kterou jsou známým způsobem tyto informace odebírány. V ostatním je zapojení stejné jako v prvním příkladném uskutečnění. Místy 8 odběru přebytků elektrické energie jsou běžné zásuvky. </p>
    <p num="89"> </p>
    <p num="90">Funkce zařízení obou příkladných uskutečněních jsou obdobné: </p>
    <p num="91"> </p>
    <p num="92">Obnovitelný zdroj 1, kterým jsou fotovoltaické panely, přeměňuje světelnou energii slunce na stejnosměrnou elektrickou energii, kterou měnič 5 známým způsobem mění na standardní střídavé napětí distribuční sítě 14. Střídavé napětí je předáváno přes elektroměr 16 pro potřeby spotřebičů 15, které jsou na tento obousměrný elektroměr 16 v odběrném místě 3 napojené a rovněž do distribuční sítě 14 v bytovém domě pro potřeby všech odběrných míst 3. Pokud je bytový dům opatřen bateriovým úložištěm 14, je elektrická energie obnovitelného zdroje 1 použita rovněž k dobíjení bateriového úložiště 4. Pokud řídící jednotka 6 z údajů získaných z měřiče 2 výkonu a indikátoru 9 stavu naplnění bateriového úložiště 4 zjistí, že je přebytek elektrické energie z obnovitelného zdroje 1, lze nadvýrobu odesílat do distribuční sítě 14 v bytovém domě, odkud je možno ji odebírat ve všech odběrných místech 3, tj. všemi elektroměry 16. Protože je zařízení opatřeno bateriovým úložištěm 4, lze jej nadvýrobou elektrické energie z obnovitelného zdroje 1 dobít. </p>
    <p num="93"> </p>
    <p num="94">Další možností využití přebytků elektrické energie je aktivovat propojením 12 příslušným spínačem 7 některé místo 8 odběru přebytků elektrické energie, které je umístěno v některém odběrném místě 3, tj. v některém bytě.  </p>
    <p num="95"> </p>
    <p num="96">Na jednotlivých místech 8 odběru přebytků elektrické energie v jednotlivých odběrných místech 3 jsou napojeny elektrické spotřebiče 15, které nejsou nezbytné, ale je vhodné je zprovoznit v případě levné ceny elektrické energie.  </p>
    <p num="97"> </p>
    <p num="98">Příkladem jsou zejména klimatizační jednotky, resp. jejich spínací elementy, které dají pokyn k sepnutí klimatizační jednotky.  </p>
    <p num="99"> </p>
    <p num="100">Na místa 8 odběru přebytků elektrické energie mohou být napojeny pouze ovládací prvky některých spotřebičů odběrných míst 3 tak, že dojde k zvýšení jejich výkonu. V tom případě je místo 8 odběru přebytků elektrické energie použito pouze jako zdroj informací k pokynu pro odběr přebytků elektrické energie. Takto může být iniciován vyšší stupeň chlazení klimatizační jednotky, a tím snížení teploty v domě z obvyklých 22 °C na 20°C. Nebo lze u mrazících boxů iniciovat pokyn pro snížení teploty, a tím využít přebytků elektrické energie z obnovitelného zdroje 1 k vyššímu podchlazení. </p>
    <p num="101"> </p>
    <p num="102">V uvedených případech je podchlazení pouze dočasné. Když v následujícím časovém období pomine přebytek elektrické energie z obnovitelného zdroje 1, dojde vypnutím spínačů 7 k vypnutí místa 8 odběru přebytků elektrické energie a návratu těchto spotřebičů do původního stavu tím, že nebudou určitou dobu odebírat elektrickou energii nebo alespoň po určitou dobu bude jejich příkon snížen. Každopádně tím dojde k finanční úspoře tím, že bude určitou dobu odebírána levná – přebytková elektrická energie, a nikoliv dražší elektrická energie v době, kdy není její přebytek.  </p>
    <p num="103"> </p>
    <p num="104">Místo 8 odběru přebytků elektrické energie tedy poskytuje elektrickou energii pouze v době, kdy je elektrická energie levná a je proto výhodné tuto elektrickou energii odebírat pro potřeby bytového domu.  </p>
    <p num="105"> </p>
    <p num="106">Zejména lze výhody míst 8 odběru přebytků elektrické energie z obnovitelného zdroje 1 použít pro ohřev užitkové vody, když se obdobně sepne elektrický ohřev teplé vody napojený na místo 8 odběru přebytků elektrické energie z obnovitelného zdroje 1 a přebytek se použije pro zvýšení teploty ohřívané užitkové vody nad obvyklou výši, což umožní následně po ukončení přebytku elektrické energie z obnovitelného zdroje 1 po určitou dobu nepoužívat již drahou elektrickou energii a ponechat klesnout teplotu teplé užitkové vody na obvyklou výši. </p>
    <p num="107"> </p>
    <p num="108">Veškeré tyto možnosti rozhoduje řídící jednotka 6 podle předem naprogramovaného algoritmu. </p>
    <p num="109"> </p>
    <p num="110">Řídící jednotka 6 při svém rozhodování může známým způsobem zohlednit údaje získané z informačního zdroje 10 spotové ceny elektrické energie a rovněž z informačního zdroje 11 predikce počasí.  </p>
    <p num="111"> </p>
    <p num="112">Spínání jednotlivých míst 8 odběru přebytků elektrické energie z obnovitelného zdroje 1 spínačem 7 je prováděno řídící jednotkou 6 pro každé místo 8 odběru přebytků elektrické energie samostatně podle algoritmu nastaveném v řídící jednotce 6.  </p>
    <p num="113"> </p>
    <p num="114">Třetí příkladné uskutečnění soupravy a její použití je zobrazeno na obr. 3. Souprava obsahuje bateriové úložiště 4 o kapacitě 500 Ah a napětí 50 V, které je opatřeno indikátorem 9 stavu naplnění bateriového úložiště 4. Dále souprava obsahuje měřič 2 výkonu fotovoltaických panelů 1, měřič 13 množství elektrické energie, řídící jednotku 6 a tři spínače 7, z nichž každý je napojen na jedno místo 8 odběru přebytků elektrické energie.  </p>
    <p num="115"> </p>
    <p num="116">Propojení jednotlivých prvků s řídící jednotkou 6 je obdobné jako u dvou předchozích příkladů uskutečnění. Rozdílem je, že souprava obsahuje střídač 17, který je po instalaci soupravy na bytový dům zapojen paralelně s měničem 5. </p>
    <p num="117"> </p>
    <p num="118">V ostatním je zařízení obdobné s prvním i druhým příkladným uskutečněním. </p>
    <p num="119"> </p>
    <p num="120">Funkce zařízení ve třetím příkladném uskutečnění je obdobná jako funkce zařízení podle druhého příkladného uskutečnění s tím rozdílem, že řídící jednotka 6 v některých případech vyhodnotí, že není zapotřebí používat měnič 5, který sice umí spolupracovat s bateriovým úložištěm 4, ale vyznačuje se menší účinností. Přitom pro provoz zařízení postačí střídač 17, který má vyšší účinnost přeměny stejnosměrného napětí z obnovitelného zdroje 1 na střídavé napětí 230 V distribuční sítě 14. V tom případě dá řídící jednotka 6 přes propojení 12 pokyn k vypnutí hybridního měniče 5 a zprovoznění střídače 17. Zařízení potom pracuje s vyšší účinností, nebude však při činnosti střídače 17 obsluhovat bateriové úložiště 4. </p>
    <p num="121"> </p>
    <p num="122"> </p>
    <p num="123">Průmyslová využitelnost </p>
    <p num="124"> </p>
    <p num="125">Technické řešení je vhodné pro využití přebytků elektrické energie z obnovitelného zdroje k účelnému využití zejména v bytových domech.  </p>
    <p num="126"> </p>
    <description-of-drawings>
      <p num="1">
        <br/>
      </p>
      <p num="2">1 - obnovitelný zdroj</p>
      <p num="3">2 - měřič výkonu</p>
      <p num="4">3 - odběrné místo</p>
      <p num="5">4 - bateriové úložiště</p>
      <p num="6">5 - měnič</p>
      <p num="7">6 - řídicí jednotka</p>
      <p num="8">7 - spínač</p>
      <p num="9">8 - místo odběru přebytků elektrické energie</p>
      <p num="10">9 - indikátor stavu naplnění bateriového úložiště (4)</p>
      <p num="11">10 - informační zdroj spotové ceny elektrické energie</p>
      <p num="12">11 - informační zdroj predikce počasí</p>
      <p num="13">12 – propojení</p>
      <p num="14">13 – měřič množství elektrické energie</p>
      <p num="15">14 – distribuční síť</p>
      <p num="16">15 – spotřebič</p>
      <p num="17">16 – elektroměr</p>
      <p num="18">17 – střídač</p>
    </description-of-drawings>
  </description>
  <claims id="claim">
    <claim num="1">
      <claim-text>Souprava pro využití přebytků elektrické energie z obnovitelného zdroje (1), vhodná zejména pro bytový dům, který je opatřen obnovitelným zdrojem (1) elektrické energie, napojeným přes
   <b> </b>měnič (5) na elektroměr (16) některého odběrného místa (3) elektrické energie, 
   <b>vyznačující se tím</b>,
   <b> </b>že sestává z řídicí jednotky (6), měřiče (2) výkonu a alespoň jednoho spínače (7) spojeného s alespoň jedním místem (8) odběru přebytků elektrické energie,přitom měřič (2) výkonu je připojen na řídicí jednotku (6) a je připojitelný na obnovitelný zdroj (1) elektrické energiea každý spínač (7) je připojen na řídicí jednotku (6) a je připojitelný na některý elektroměr (16),přitom řídicí jednotka (6) je uzpůsobená zejména pro:-      snímání údajů z měřiče (2) výkonu,-      snímání údajů z elektroměru (16),-      získávání údajů z měniče (5),-      ovládání spínačů (7),-      vyhodnocování získaných údajů a rozhodování, zda je momentálně vyráběná elektrická  energie přebytková.
  </claim-text>
    </claim>
    <claim num="2">
      <claim-text>Souprava pro využití přebytků elektrické energie z obnovitelného zdroje (1), vhodná zejména pro bytový dům, který je opatřen obnovitelným zdrojem (1) elektrické energie, napojeným přes
   <b> </b>měnič (5) na elektroměr (16) některého odběrného místa (3) elektrické energie, 
   <b>vyznačující se tím</b>,
   <b> </b>že sestává z řídicí jednotky (6), měřiče (2) výkonu a alespoň jednoho spínače (7) spojeného s alespoň jedním místem (8) odběru přebytků elektrické energie,přitom měřič (2) výkonu je připojen na řídicí jednotku (6) a je připojitelný na obnovitelný zdroj (1) elektrické energiea každý spínač (7) je připojen na řídicí jednotku (6) a je připojitelný na některý elektroměr (16),přitom řídicí jednotka (6) je uzpůsobená zejména pro:-      snímání údajů z měřiče (2) výkonu,-      snímání údajů z elektroměru (16),-      získávání údajů z měniče (5),-      ovládání spínačů (7),-      vyhodnocování získaných údajů a rozhodování, zda je momentálně vyráběná elektrická  energie přebytková,přičemž souprava dále obsahuje měřič (13) množství elektrické energie, připojitelný mezi měnič (5) a elektroměr (16), který je propojený s řídicí jednotkou (6).
  </claim-text>
    </claim>
    <claim num="3">
      <claim-text>Souprava pro využití přebytků elektrické energie z obnovitelného zdroje (1), vhodná zejména pro bytový dům, který je opatřen obnovitelným zdrojem (1) elektrické energie, napojeným přes
   <b> </b>měnič (5) na elektroměr (16) některého odběrného místa (3) elektrické energie, 
   <b>vyznačující se tím</b>, že sestává z řídicí jednotky (6), měřiče (2) výkonu a alespoň jednoho spínače (7) spojeného s alespoň jedním místem (8) odběru přebytků elektrické energie,přitom měřič (2) výkonu je připojen na řídicí jednotku (6) a je připojitelný na obnovitelný zdroj (1) elektrické energiea každý spínač (7) je připojen na řídicí jednotku (6) a je připojitelný na některý elektroměr (16),přitom řídicí jednotka (6) je uzpůsobená zejména pro:-      snímání údajů z měřiče (2) výkonu,-      snímání údajů z elektroměru (16),-      získávání údajů z měniče (5),-      ovládání spínačů (7),-      vyhodnocování získaných údajů a rozhodování, zda je momentálně vyráběná elektrická  energie přebytková,přičemž souprava dále obsahuje měřič (13) množství elektrické energie, připojitelný mezi měnič (5) a elektroměr (16), který je propojený s řídicí jednotkou (6),a dále obsahuje bateriové úložiště (4), které je opatřeno indikátorem (9) stavu naplnění bateriového úložiště (4), které je propojeno s řídicí jednotkou (6).
  </claim-text>
    </claim>
    <claim num="4">
      <claim-text>Souprava pro využití přebytků elektrické energie z obnovitelného zdroje (1), vhodná zejména pro bytový dům, který je opatřen obnovitelným zdrojem (1) elektrické energie, napojeným přes
   <b> </b>měnič (5) na elektroměr (16) některého odběrného místa (3) elektrické energie, 
   <b>vyznačující se tím</b>,
   <b> </b>že sestává z řídicí jednotky (6), měřiče (2) výkonu a alespoň jednoho spínače (7) spojeného s alespoň jedním místem (8) odběru přebytků elektrické energie,přitom měřič (2) výkonu je připojen na řídicí jednotku (6) a je připojitelný na obnovitelný zdroj (1) elektrické energiea každý spínač (7) je připojen na řídicí jednotku (6) a je připojitelný na některý elektroměr (16),přitom řídicí jednotka (6) je uzpůsobená zejména pro:-      snímání údajů z měřiče (2) výkonu,-      snímání údajů z elektroměru (16),-      získávání údajů z měniče (5),-      ovládání spínačů (7),-      vyhodnocování získaných údajů a rozhodování, zda je momentálně vyráběná elektrická  energie přebytková,přičemž souprava dále obsahuje měřič (13) množství elektrické energie, připojitelný mezi měnič (5) a elektroměr (16), který je propojený s řídicí jednotkou (6),a dále obsahuje bateriové úložiště (4), které je opatřeno indikátorem (9) stavu naplnění bateriového úložiště (4), které je propojeno s řídicí jednotkou (6),přičemž na vstup řídicí jednotky (6) je napojen informační zdroj (11) predikce počasí a informační zdroj (10) spotové ceny elektrické energie a řídicí jednotka (6) je uzpůsobena pro příjem informací z informačního zdroje (11) predikce počasí a informační zdroj (10) spotové ceny elektrické energie.
  </claim-text>
    </claim>
  </claims>
  <drawings id="draw">
    <figure num="1">
      <img file="2513888img0001.jpg" img-content="drawing" img-format="jpg" wi="313" he="343"/>
    </figure>
    <figure num="2">
      <img file="2513888img0002.jpg" img-content="drawing" img-format="jpg" wi="388" he="373"/>
    </figure>
    <figure num="3">
      <img file="2513888img0004.jpg" img-content="drawing" img-format="jpg" wi="408" he="352"/>
    </figure>
  </drawings>
</ep-patent-document>
